StandardsInternational : IEC 60228
National : IRAM 63005; NTP-IEC 60228
For overhead primary distribution networks in horizontal arrangements. The installation will be performed in wooded areas in order to reduce the contact of environmental impact. This is not an insulated cable, it is a protected cable.
1. Conductor: Compact stranded aluminium 1350, class 2 (with longitudinally watertight between the conductor).
2. Semi-conductor: Extruded compound over conductor.
3. Sheath: Antitracking cross linked polyethylene XLPE compound.
With longitudinally watertight between the conductor. Good properties against heat aging. Resistance to abrasion, moisture, sunlight and tracking. Protection should not be considered as insulation.
INDECO S.A. CAPI-MT(OL) 13,2 kV - Section - Year - Sequential length.
Non returnable wooden reels.
NTP-IEC 60228: Conductors of insulated cables.
IEC 60228: Conductors of insulated cables.
IRAM 63005: Unipolar protected-not isolated cables for overhead power lines with nominal voltages (U) from 13,2 kV to 33 kV (Um = 36 kV).
|Conductor material||aluminum Alloy 1350|
|Time of application Dielectric strength core to screen DC||5min.|
|Maximum operating temperature||90°C|
|Overload maximum core temperature||130°C|
|Short-circuit max. conductor temperature||250°C|
|See all products|