NYS2Y(80°)-C 0,6/1 kV; Screen Elect. Resist. PH: 2,0 Ohm/km; Anti-Rodent
In factories, substations or power plants.
StandardsInternational : IEC 60228; IEC 60332-1-2; IEC 60502-1; IEC 60684-2; IEC 60754-1; IEC 60754-2; IEC 61034-2
National : ICEA S-95-658; NTP-IEC 60228; NTP-IEC 60502-1; UL 2556
In factories, substations or power plants; for control, measuring or signaling systems.
1. Conductor: Soft copper, class 2.
2. Insulation: Compound polyvinyl chloride PVC.
3. Inner covering: Compound polyvinyl chloride PVC.
4. Screen: Copper wires.
5. Tape: Polyester.
6. Outer sheath: LLDPE linear low density polyethylene anti-rodent compound.
Good electrical and mechanical properties. Resistance to abrasion, moisture and sunlight. Adequate resistance to greases and oils. Flame retardant. Low emission dense smoke and halogen free. Resistance to attack by rodents.
From 1,5 mm2 up to 4 mm2.
INDECO S.A. NYS2Y(80º)-C 0,6/1 kV - Nb. conductors x section - Year - Sequential length.
Non returnable wooden reels.
Insulation: Black with white numbers.
Outer sheath: Black.
NTP-IEC 60228: Conductors of insulated cables.
NTP-IEC 60502-1: Power cables with extruded insulation and their accessories for rated voltages from 1 kV and 3 kV.
IEC 60228: Conductors of insulated cables.
IEC 60502-1: Power cables with extruded insulation and their accessories for rated voltages from 1 kV and 3 kV.
IEC 60332-1-2: Test for vertical flame propagation for a single insulated wire or cable - Procedure for 1 kW pre-mixed flame.
UL 2556: Wire and Cable Test Methods. Section 9.3: FT1 (Vertical-Specimen) Flame Test.
IEC 60684-2: Flexible insulating sleeving - Part 2: Methods of test.
IEC 60754: Test on gases evolved during combustion of materials from cables.
Part 1: Determination of the halogen acid gas content.
Part 2: Determination of acidity (by pH measurement) and conductivity.
IEC 61034-2: Measurement of smoke density of cables burning under defined conditions.
ICEA S-93-639: 5-46 kV Shielded Power Cable for Use in the Transmission and Distribution of Electric Energy. Section 9.4.2: Oil Immersion Test.
UL 2556: Wire and Cable Test Methods. Section 126.96.36.199: Carbon-Arc and Xenon-Arc Tests- Sunlight resistance.
|Conductor material||Soft copper|
|Core identification||Black cores with white numbers|
|Electrostatic shielding||Helically applied copper wires|
|Halogen free||IEC 60754-1|
|Dielectric strength core to screen DC, min.||3.5kV|
|Time of application Dielectric strength core to screen DC||5min.|
|Resistance of the screen||2.0Ohm/km|
|Rodent protection||ARS (Anti rodent sheath)|
|U.V resistance||UL 2556 - Sunlight Resistance|
|Oil resistance||ICEA S-95-658|
|Gases toxicity||Low toxicity to IEC 60684-2|
|Gases corrosivity||Low pH Corrosivity IEC 60754-2|
|Smoke density||IEC 61034-2|
|Flame retardant||IEC 60332-1-2; FT1|
|Maximum operating temperature||80°C|
|Overload maximum core temperature||100°C|
|Short-circuit max. conductor temperature||160°C|
|See all products|