N2XSYRAY 26/45 kV; IEC 60332-3-22 Cat. A; Anti-Termite
Power distribution in medium voltage.
StandardsInternational : IEC 60228; IEC 60332-1; IEC 60332-3 Cat.A; IEC 60754-1; IEC 60840; UIC 895
National : NTP-IEC 60228; SAE J-1127; UL 1581
Power distribution in medium voltage. As transformer feeders in substations. In power plants, industrial and operation installations, in residential areas and mining installations, in dry or wet locations; where mechanical strength is required.
1. Conductor: Compact stranded soft copper, class 2.
2. Inner semi-conductor: Extruded.
3. Insulation: Cross linked polyethylene XLPE.
4. External semi-conductor: Extruded strippable.
These last three components extruded CV (continuous vulcanization) triple extrusion.
5. Screen: Copper tape (0.127 mm), minimum overlap 50%.
6. Separation sheath: Compound polyvinyl chloride PVC.
7. Armour: 1350 aluminium wires.
8. Fire protection tape.
9. Outer sheath: Anti-flame and anti-termite PVC.
Its armour provides additional mechanical protection. Resistance to abrasion, moisture and sunlight. Resistance to combustible liquids and oils according to UIC 895 OR. Resistance to sulfuric acid according to SAE J1127. Resistance to aliphatic and aromatic hydrocarbon according to UL 44. Fire retardant according to IEC 60332-3-22 Cat. A. Low halogen content according to IEC 60754-1. Resistance to attack by termites.
From 150 mm2 up to 400 mm2.
INDECO S.A. N2XSYRAY 26/45 kV - Section - Year - Sequential length.
Non returnable wooden reels.
Outer sheath: Red-UV.
NTP-IEC 60228: Conductors of insulated cables.
IEC 60228: Conductors of insulated cables.
IEC 60840: Power cables with extruded insulation and their accessories for rated voltages above 30 kV (Um = 36 kV) up to 150 kV (Um = 170 kV) - Test methods and requirements.
IEC 60332-1: Test for vertical flame propagation for a single insulated wire or cable.
IEC 60332-3-22: Test for vertical flame spread of vertically-mounted bunched wires or cables - Category A.
IEC 60754-1: Test on gases evolved during combustion of materials from cables - Part 1: Determination of the halogen acid gas content.
SAE J1127: Surface vehicle standard. Battery cable. Clause 6.7 (Fluid Compatibility): Resistance to Sulfuric Acid.
UIC 895 OR: Technical specification for the supply of insulated electric cables for railway vehicles - Oil Resistant.
UL 1581 Section 1200 (Sunlight resistance): Reference standard for electrical wires, cables, and flexible cords - Carbon-Arc and Xenon-Arc Tests- Sunlight resistance.
|Material of the inner semi-conductor||Extruded|
|Material of the external semi-conductor||Extruded strippable|
|Screen||Copper tape, helically|
|Armour type||Aluminium Wire|
|Outer sheath||Flame retardant Antitermite PVC|
|Rated Voltage Uo/U (Um)||26/45 kV|
|Mechanical resistance to impacts||Good|
|Flame retardant||IEC 60332-1|
|Fire retardant||IEC 60332-3 Cat.A|
|Slightly halogenous||IEC 60754-1|
|Oil resistance||UIC 895 OR|
|U.V resistance||UL 1581 - Sunlight Resistance|
|Resistant to termites||Yes|
|Maximum operating temperature||90°C|
|Overload maximum core temperature||130°C|
|Short-circuit max. conductor temperature||250°C|
|See all products|
Products and services
Docs and info
Conductor cross section
Wire diameter (mm²)