CAPI-MT 15 kV; Inner sheath: XLPE; ABNT-NBR 11873
For overhead primary distribution networks.
StandardsNational : ABNT NBR 11873; ASTM B 231
For overhead primary distribution networks in horizontal arrangements. The installation will be performed in wooded areas in order to reduce the contact of environmental impact. This is not an insulated cable, it is a protected cable.
1. Conductor: Compact stranded aluminium 1350, class B.
2. Semi-conductor: Extruded.
3. Inner Sheath: XLPE cross linked polyethylene.
4. Outer Sheath: HDPE antitracking high density polyethylene.
Good properties against heat aging. Good properties against heat aging. Resistance to abrasion, moisture, sunlight and to surface discharges (tracking and carbonization). Protection should not be considered as insulation.
INDECO S.A - CAPI MT - Protected Cable 15 kV, Do not Touch - Gauge - Year - Sequential length.
Non returnable wooden reels.
ASTM B231: Concentric-Lay-Stranded Aluminum 1350 Conductors.
ABNT-NBR 11873: Covered cables with polymeric material for overhead distribution lines in spacers for voltages 13,8 kV up to 34,5 kV.
|Conductor material||aluminum Alloy 1350|
|Material of the inner semi-conductor||Extruded|
|Outer sheath||HDPE - Antitracking|
|Dielectric strength core to screen DC, min.||18.0kV|
|Time of application Dielectric strength core to screen DC||5min.|
|Maximum operating temperature||75°C|
|Overload maximum core temperature||95°C|
|Short-circuit max. conductor temperature||150°C|
|See all products|