CAAI 0,6/1 kV Covered AAAC Neutral; with Public Lighting; E-BT-002
For overhead secundary distribution networks.
StandardsInternational : IEC 60228; IEC 60811-402; IEC 60811-502; IEC 60811-507; IEC 60811-511
National : NTP 370.254; NTP 370.258; NTP-IEC 60228
For urban and rural overhead secundary distribution networks, with voltages up to 1000 V.
1. Conductor: Aluminium 1350, class 2.
2. Public lighting: Aluminium 1350 - XLPE.
3. Insulated neutral messenger: AAAC - All Alloy Aluminium - XLPE.
4. Insulation: Cross linked polyethylene XLPE.
Decreases energy theft, cross-linked polyethylene allows more current capacity and high insulation resistance, lower inductive reactance than with bare conductors, used in overhead distribution lines. Increased safety due to its mechanical strength and toughness of the insulation. Insulators are not necessary for installation. Resistance to abrasion, weather and sunlight.
INDECO S.A. CAAI 0,6/1 kV - (Nb. Cores x Section) + (Nb. conductors x public lightning section) + NA(Neutral messenger section) - Year - Sequential length.
Non returnable wooden reels.
Black, see core identification.
NTP-IEC 60228: Conductors of insulated cables.
NTP 370.254: Cables for overhead distribution networks self-supporting XLPE insulated of rated voltages up to and including 0,6/1 kV.
NTP 370.258: Conductors with aluminum round wires stranded concentrically for overhead networks.
E-BT-002: Pre-assembled cables for low voltage overhead lines.
IEC 60228: Conductors of insulated cables.
IEC 60811- 201: Electric and optical fibr cables - Test methods for non- metallic materials - Part 201: General tests - Measurement of insulation thickness.
IEC 60811- 401: Electric and optical fibr cables - Test methods for non- metallic materials - Part 401: Miscellaneous tests - Thermal ageing methods -Ageing in an air oven.
IEC 60811- 501: Electric and optical fibr cables - Test methods for non- metallic materials - Part 501: Mechanical tests - Test for determining the mechanical properties of insulating and sheating.
IEC 60811-402: Water absorption test.
IEC 60811-502: Shrinkage test for isolations.
IEC 60811-507: Hot elongation test for crosslinked materials.
IEC 60811-511: Measurement of hot melt index of polyethylene compounds.
|Phase Conductor Type||AAC - All Aluminium Conductor|
|Core identification||Rib markings|
|Neutral messenger||AAAC - All Alloy Aluminium Conductor|
|Rated Voltage Uo/U (Um)||0.6/1 kV|
|Time of application Dielectric strength core to screen DC||5min.|
|Bending factor when installed||4(xD)|
|Maximum operating temperature||90°C|
|Overload maximum core temperature||130°C|
|Short-circuit max. conductor temperature||250°C|
|See all products|