StandardsInternational : IEC 60332-1-2
National : ASTM B 231; ICEA S-94-649; UL 2556
Power distribution in medium voltage. As transformer feeders in substations. In power plants, industrial and operation installations, in residential areas and mining installations, in dry or wet locations.
1. Conductor: Compact stranded aluminium 1350, class B (with longitudinally watertight between and over the core conductor).
2. Inner semi-conductor: Extruded.
3. Insulation: Cross linked polyethylene XLPE-TR (Tree retardant).
4. External semi-conductor: Extruded strippable.
These last three components extruded CV (continuous vulcanization) triple extrusion in dry cure process.
5. Concentric conductor: Copper wires helically applied. (1/3) concentric neutral according to ICEA S-94-649.
6. Tape: Polyester.
7. Outer sheath: Compound polyvinyl chloride PVC.
To 100% for insulation level. Excellent properties against heat aging. With longitudinally watertight between and over the core conductor. Resistance to abrasion, moisture and sunlight. Adequate resistance to greases and oils. Flame retardant.
INDECO S.A. NA2XCY(OL) 15 kV - Gauge - NC33 - Year - Sequential length.
Non returnable wooden reels.
Outer sheath: Black.
ASTM B231: Standard Specification for Concentric-Lay-Stranded Aluminum 1350 Conductors.
ICEA S-94-649: Concentric Neutral Cables Rated 5 Through 46 kV.
IEC 60332-1-2: Test for vertical flame propagation for a single insulated wire or cable - Procedure for 1 kW pre-mixed flame.
UL 2556: Wire and Cable Test Methods. Section 9.3: FT1 (Vertical-Specimen) Flame Test.
UL 2556: Wire and Cable Test Methods. Section 126.96.36.199: Carbon-Arc and Xenon-Arc Tests- Sunlight resistance.
|Conductor material||aluminum Alloy 1350|
|Material of the inner semi-conductor||Extruded|
|Material of the external semi-conductor||Extruded strippable|
|Concentric conductor||Copper wires helically applied|
|Dielectric strength core to screen DC, min.||35.0kV|
|Time of application Dielectric strength core to screen DC||5min.|
|Voltage for partial discharge test||35.0kV|
|Maximal partial discharge test||5pC|
|Longitudinal water tightness||Yes|
|U.V resistance||UL 2556 - Sunlight Resistance|
|Flame retardant||IEC 60332-1-2; FT1|
|Maximum operating temperature||90°C|
|Overload maximum core temperature||130°C|
|Short-circuit max. conductor temperature||250°C|
|See all products|
Products and services
Docs and info
Concentric Neutral Nb of wires