NA2XY 0,6/1 kV Multi-core with Isolated Grounding Conductor
General use as power cable, for fixed installations.
StandardsInternational : IEC 60228; IEC 60332-1-2; IEC 60502-1; IEC 60811-401; IEC 60811-402; IEC 60811-409; IEC 60811-501; IEC 60811-502; IEC 60811-504; IEC 60811-505; IEC 60811-506; IEC 60811-507; IEC 60811-508; IEC 60811-509
National : NTP-IEC 60228; NTP-IEC 60502-1; UL 2556
General application as power cable. In low voltage distribution power networks, industrial installations, in buildings and operation stations. In fixed installations, indoor and outdoor areas (trays, gutters, staples). It can be installed in ducts, in dry or wet locations.
1. Conductor: Aluminium 1350 compacted, class 2.
2. Insulation: Cross linked polyethylene XLPE.
3. Insulated grounding conductor: Aluminium 1350, class 2 - XLPE
4. Filler: Compound polyvinyl chloride PVC.
5. Outer sheath: Compound polyvinyl chloride PVC.
Good electrical and mechanical properties. Cross-linked polyethylene insulation allows greater power capacity under any operating condition, minimum dielectric losses, high insulation resistance. The PVC outer sheath allows an adequate resistance to greases, oils and abrasion. Resistance to sunlight. Flame retardant.
From 70 mm2 up to 300 mm2.
INDECO S.A - NA2XY 0,6/1 kV - Nb. cores x Section + Grounding Cond. Section - Year - Sequential length.
Non returnable wooden reels.
Insulation: See core identification.
Outer sheath: Black.
NTP-IEC 60228: Conductors of insulated cables.
NTP-IEC 60502-1: Power cables with extruded insulation and their accessories for rated voltages from 1 kV and 3 kV.
IEC 60228: Conductors of insulated cables.
IEC 60502-1: Power cables with extruded insulation and their accessories for rated voltages from 1 kV and 3 kV.
IEC 60332-1-2: Test for vertical flame propagation for a single insulated wire or cable - Procedure for 1 kW pre-mixed flame.
UL 2556: Wire and Cable Test Methods. Section 9.3:FT1 (Vertical-Specimen) Flame Test.
IEC 60811-401: Thermal ageing methods -Ageing in an air oven.
IEC 60811-402: Water absorption test.
IEC 60811-409: Mass loss test for thermoplastic insulations and covers.
IEC 60811-501: Test for determining the mechanical properties of insulating and sheating.
IEC 60811-502: Shrinkage test for isolations.
IEC 60811-504: Bending test at low temperature for insulation and covers.
IEC 60811-505: Low temperature elongation test for insulations and covers.
IEC 60811-506: Impact test at low temperature for insulations and covers.
IEC 60811-507: Hot elongation test for crosslinked materials.
IEC 60811-508: High temperature pressure tests for insulations and covers.
IEC 60811-509: Tests of resistance to cracking of the insulations and covers (thermal shock).
UL 2556: Wire and Cable Test Methods. Section 126.96.36.199:Carbon-Arc and Xenon-Arc Tests- Sunlight resistance.
|Conductor material||aluminum Alloy 1350|
|Rated Voltage Uo/U (Um)||0.6/1 kV|
|Time of application Dielectric strength core to screen DC||5min.|
|U.V resistance||UL 2556 - Sunlight Resistance|
|Flame retardant||IEC 60332-1-2; FT1|
|Maximum operating temperature||90°C|
|Overload maximum core temperature||130°C|
|Short-circuit max. conductor temperature||250°C|
|See all products|
Products and services
Docs and info
Core Identification L.V with ground cond.
Number of cores
Black + (yellow or green or yellow/green or green/yellow)
White + black, white + red, white + blue, blue + brown, blue + black or black + red + (yellow or green or yellow/green or green/yellow)
White + black + red, black + red + blue, brown + black + grey or blue + brown + black + (yellow or green or yellow/green or green/yellow)
White + black + red + blue, blue + brown + black + grey + (yellow or green or yellow/green or green/yellow)