FREETOX N2XCOH 0,6/1 kV; VFD
Power or control cable, for use with variable frequency drives (VFD).
StandardsInternational : IEC 60228; IEC 60332-1-2; IEC 60332-3-24 Cat.C; IEC 60502-1; IEC 60684-2; IEC 60754-1; IEC 60754-2; IEC 61034-2
National : ICEA S-95-658; NTP-IEC 60228; NTP-IEC 60502-1; UL 2556
In factories, substations or power plants where there is a lot of electrical noise or transient, for control, measuring or signaling systems, for connection between the variable frequency drive (VFD) and the motor; reducing the electromagnetic interferences. Direct application in places with high public attendance. Not recommended for outdoor installations.
1. Conductor: Soft copper, class 2.
2. Insulation: Cross linked polyethylene XLPE.
3. 03 Bare grounding conductors: Soft copper, class 2.
4. Inner sheath: HFFR halogen free thermoplastic compound.
5. Screen: Concentric conductor (Copper wires helically applied) + Shield static (50% overlapped copper tape).
6. Outer sheath: HHFFR halogen free thermoplastic compound.
Lower dielectric losses, high insulation resistance. Adequate shielding to electromagnetic transients. The inner and outer sheath have the following characteristics: Fire retardant, low emission of dense smoke and halogen free. Adequate resistance to oils.
INDECO S.A. FREETOX N2XCOH 0,6/1 kV - (Nb. cores x Section) + (Nb. cond. x Ground. cond. section) + (Concentric cond. section) - Year - Sequential length.
Non returnable wooden reels.
Outer sheath: Black.
NTP-IEC 60228: Conductors of insulated cables.
NTP-IEC 60502-1: Power cables with extruded insulation and their accessories for rated voltages from 1 kV and 3 kV.
IEC 60228: Conductors of insulated cables.
IEC 60502-1: Power cables with extruded insulation and their accessories for rated voltages from 1 kV and 3 kV.
IEC 60332-1-2: Test for vertical flame propagation for a single insulated wire or cable - Procedure for 1 kW pre-mixed flame.
UL 2556: Wire and Cable Test Methods. Section 9.3: FT1 (Vertical-Specimen) Flame Test.
IEC 60332-3-24: Test for vertical flame spread of vertically-mounted bunched wires or cables - Category C.
IEC 60684-2: Flexible insulating sleeving - Part 2: Methods of test.
IEC 60754-1 and IEC 60754-2 : Test on gases evolved during combustion of materials from cables - Part 1: Determination of the halogen acid gas content. Part 2: Determination of acidity (by pH measurement) and conductivity.
IEC 61034-2: Measurement of smoke density of cables burning under defined conditions.
ICEA S-95-658: Power cables rated 2000 volts or less for the distribution of electrical energy. Section 6.4.2: Oil Immersion Test.
|Conductor material||Soft copper|
|Inner sheath||Halogen free compound|
|Concentric conductor||Copper wires helically applied|
|Outer sheath||Halogen free thermoplastic compound|
|Halogen free||IEC 60754-1|
|Dielectric strength core to screen DC, min.||3.5kV|
|Time of application Dielectric strength core to screen DC||5min.|
|Electro magnetic interference resistance||Yes|
|Oil resistance||ICEA S-95-658|
|Gases toxicity||Low toxicity to IEC 60684-2|
|Gases corrosivity||Low pH Corrosivity IEC 60754-2|
|Smoke density||IEC 61034-2|
|Flame retardant||IEC 60332-1-2; FT1|
|Fire retardant||IEC 60332-3-24 Cat.C|
|Maximum operating temperature||90°C|
|Overload maximum core temperature||130°C|
|Short-circuit max. conductor temperature||250°C|
|See all products|