FREETOX N2XOH-C 0,6/1 kV; with ground. conductor
Special application in places with poor ventilation and places public attendance high.
StandardsInternational : IEC 60228; IEC 60332-1-2; IEC 60332-3-24 Cat.C; IEC 60502-1; IEC 60684-2; IEC 60754-1; IEC 60754-2; IEC 61034-2
National : ICEA S-95-658; NTP-IEC 60228; NTP-IEC 60502-1; UL 2556
In industrial plants, for systems of motor control, lighting, signaling and overal equipment interconnection, control circuits of automatic machines. Direct application in places with public attendance high. Not recommended for outdoor installations
1. Conductor: Compressed soft copper, class 2.
2. Insulation: Cross linked polyethylene XLPE.
3. Insulated grounding conductor: Soft copper, class 2 - Cross linked polyethylene XLPE.
4. Filler: Halogen free thermoplastic compound.
5. Outer sheath: Halogen free thermoplastic compound HFFR.
Lower dielectric losses, high insulation resistance. The outer sheath has the following characteristics: Fire retardant, low emission dense smoke and halogen free.
From 1.5 mm2, up to 2.5 mm2.
INDECO S.A FREETOX N2XOH-C 0.6/1 kV - Nb conductors x section + ground section - Year - Sequential length.
Non returnable wooden reels.
Insulation: for conductors: black with white numbers and for ground conductor: yellow.
Outer sheath: Black.
NTP-IEC 60228: Conductors of insulated cables.
NTP-IEC 60502-1: Power cables with extruded insulation and their accessories for rated voltages from 1 kV and 3 kV.
IEC 60228: Conductors of insulated cables.
IEC 60502-1: Power cables with extruded insulation and their accessories for rated voltages from 1 kV and 3 kV.
IEC 60332-1-2: Test for vertical flame propagation for a single insulated wire or cable - Procedure for 1 kW pre-mixed flame.
UL 2556: Wire and Cable Test Methods.
Section 9.3: FT1 (Vertical-Specimen) Flame Test.
IEC 60332-3-24: Test for vertical flame spread of vertically-mounted bunched wires or cables - Category C.
IEC 60684-2: Flexible insulating sleeving - Part 2: Methods of test.
IEC 60754: Test on gases evolved during combustion of materials from cables.
Part 1: Determination of the halogen acid gas content.
Part 2: Determination of acidity (by pH measurement) and conductivity.
IEC 61034-2: Measurement of smoke density of cables burning under defined conditions.
ICEA S-95-658: Power cables rated 2000 volts or less for the distribution of electrical energy.
Section 6.4.2: Oil: Oil Immersion Test.
|Conductor material||Soft copper|
|Core identification||Black cores with white numbers|
|Outer sheath||Halogen free thermoplastic compound|
|Halogen free||IEC 60754-1|
|Dielectric strength core to screen DC, min.||3.5kV|
|Time of application Dielectric strength core to screen DC||5min.|
|Oil resistance||ICEA S-95-658|
|Gases toxicity||Low toxicity to IEC 60684-2|
|Gases corrosivity||Low pH Corrosivity IEC 60754-2|
|Smoke density||IEC 61034-2|
|Flame retardant||IEC 60332-1-2; FT1|
|Fire retardant||IEC 60332-3-24 Cat.C|
|Maximum operating temperature||90°C|
|Overload maximum core temperature||130°C|
|Short-circuit max. conductor temperature||250°C|
|See all products|