FREETOX N2XSOH-C 0,6/1 kV FB; with insulated ground condcutor
In factories, substations or power plants.
StandardsInternational : IEC 60228; IEC 60332-1-2; IEC 60332-3-24 Cat.C; IEC 60502-1; IEC 60684-2; IEC 60754-1; IEC 60754-2; IEC 61034-2
National : ICEA S-95-658; NTP-IEC 60228; NTP-IEC 60502-1; UL 2556
In factories, substations or power plants where there is a lot of electrical noise or transient, for control, measuring or signaling systems. Direct application in places with public attendance high. Not recommended for outdoor installations.
1. Conductor: Flexible soft copper, class 5.
2. Insulation: Cross linked polyethylene XLPE.
3. Insulated grounding conductor: Flexible soft copper, class 2 - XLPE.
4. Inner covering: HFFR halogen free thermoplastic compound.
5. Screen: Copper tapes.
6. Outer sheath: HFFR halogen free thermoplastic compound.
Minimum dielectric losses, high insulation resistant. Adequate transient shield. The outer sheath has the following characteristics: Fire retardant, low emission dense smoke and halogen free. Adequate resistance to oil.
INDECO S.A. FREETOX N2XSOH-C 0,6/1 kV - (N° Conductors x section) + Grounding cond. section - FB - Year - Sequential length
Non returnable wooden reels.
Insulation: See core identification.
Outer sheath: Black.
NTP-IEC 60228: Conductors of insulated cables.
NTP-IEC 60502-1: Power cables with extruded insulation and their accessories for rated voltages from 1 kV and 3 kV.
IEC 60228: Conductors of insulated cables.
IEC 60502-1: Power cables with extruded insulation and their accessories for rated voltages from 1 kV and 3 kV.
IEC 60332-1-2: Test for vertical flame propagation for a single insulated wire or cable - Procedure for 1 kW pre-mixed flame.
UL 2556: Wire and Cable Test Methods. Section 9.3: FT1 (Vertical-Specimen) Flame Test.
IEC 60332-3-24: Test for vertical flame spread of vertically-mounted bunched wires or cables - Category C.
IEC 60684-2: Flexible insulating sleeving - Part 2: Methods of test.
IEC 60754-1: Test on gases evolved during combustion of materials from cables - Part 1: Determination of the halogen acid gas content.
IEC 60754-2: Test on gases evolved during combustion of materials from cables - Part 2: Determination of acidity (by pH measurement) and conductivity.
IEC 61034-2: Measurement of smoke density of cables burning under defined conditions.
ICEA S-95-658: Power cables rated 2000 volts or less for the distribution of electrical energy. Section 6.4.2: Oil: Oil Immersion Test.
|Conductor material||Soft copper|
|Screen||Copper tape, helically|
|Outer sheath||Halogen free thermoplastic compound|
|Halogen free||IEC 60754-1|
|Dielectric strength core to screen DC, min.||3.5kV|
|Time of application Dielectric strength core to screen DC||5min.|
|Oil resistance||ICEA S-95-658|
|Gases toxicity||Low toxicity to IEC 60684-2|
|Gases corrosivity||Low pH Corrosivity IEC 60754-2|
|Smoke density||IEC 61034-2|
|Flame retardant||IEC 60332-1-2; FT1|
|Fire retardant||IEC 60332-3-24 Cat.C|
|Maximum operating temperature||90°C|
|Overload maximum core temperature||130°C|
|Short-circuit max. conductor temperature||250°C|
|See all products|
Products and services
Docs and info
Core Identification L.V
Number of cores
White + black, black + blue, blue + brown or black + red
White + black + red, brown + black + grey, blue + brown + black or black + red + blue
White + black + red + blue or blue + brown + black + grey
White + black + red + blue + brown