StandardsInternational : FT4 IEEE1202 ; IEC 60332-1-2; IEC 60754-1; UIC 895
National : ASTM B 8; ICEA S-93-639; SAE J-1127; UL 2556; UL 44
Power distribution in medium voltage. As transformer feeders in substations. In power plants, industrial and operation installations, in residential areas mining installations where high mechanical strength is required. The interlocked aluminum armour gives greater flexibility compared to the traditional steel armour and the type of conformation of the same make has a high resistance to loads that could be placed on it.
1. Conductor: Compact stranded soft copper, class B.
2. Inner semi-conductor: Extruded.
3. Insulation: Cross linked polyethylene XLPE-TR (Tree retardant).
4. External semi-conductor: Extruded strippable.
These last three components extruded CV (continuous vulcanization) triple extrusion.
5. Screen: Copper tapes.
6. Separation sheath: Anti-flame compound polyvinyl chloride PVC.
7. Armour: Interlocked Alumninium tape.
8. Outer sheath: Anti-flame compound polyvinyl chloride PVC.
Excellent properties against heat aging. Insulation level of 100%. Its armour provides additional mechanical protection and provides flexibility compared with other types of armour. Resistance to moisture, abrasion and sunlight. Resistance to combustible liquids and oils according to UIC 895 OR and Gasoline Resistant GR I according to UL 44. Resistance to sulfuric acid according to SAE J1127. Low halogen content according to IEC 60754-1. Fire retardant according to IEEE 1202/FT-4. Resistance to attack by rodents.
From 4/0 AWG up to 500 kcmil.
INDECO S.A. N2XSEYBIY(INTERLOCK) 25 kV - Gauge - Year - Sequential Length.
Non returnable wooden reels.
Outer sheath: Black.
ASTM B8: Concentric-Lay-Stranded copper conductors, hard, medium-hard, or soft.
ICEA S-93-639: 5 - 46 kV Shielded Power Cable for use in the transmission and distribution of electric energy.
IEC 60332-1-2: Test for vertical flame propagation for a single insulated wire or cable - Procedure for 1 kW pre-mixed flame.
UL 2556: Wire and Cable Test Methods. Section 9.3: FT1 (Vertical-Specimen) Flame Test.
FT4/IEEE 1202: Vertical Tray Flame Test.
IEC 60754-1: Test on gases evolved during combustion of materials from cables - Part 1: Determination of the halogen acid gas content.
SAE J1127: Surface vehicle standard. Battery cable. Clause 6.7 (Fluid Compatibility) : Resistance to Sulfuric Acid.
UL 44: Thermoset-Insulated Wires and Cables. Section 5.17: Gasoline and oil resistance.
UIC 895 OR: Technical specification for the supply of insulated electric cables for railway vehicles - Oil Resistant.
UL 2556: Wire and Cable Test Methods. Section 18.104.22.168: Carbon-Arc and Xenon-Arc Tests- Sunlight resistance.
|Conductor material||Soft copper|
|Material of the inner semi-conductor||Extruded|
|Material of the external semi-conductor||Extruded strippable|
|Screen||Copper tape, helically|
|Armour type||Interlocked aluminum tape|
|Outer sheath||Flame retardant PVC|
|Dielectric strength core to screen DC, min.||52.0kV|
|Time of application Dielectric strength core to screen DC||5min.|
|Voltage for partial discharge test||52.0kV|
|Maximal partial discharge test||5pC|
|Mechanical resistance to impacts||Excellent|
|Slightly halogenous||IEC 60754-1|
|U.V resistance||UL 2556 - Sunlight Resistance|
|Flame retardant||IEC 60332-1-2; FT1|
|Fire retardant||FT4/IEEE 1202|
|Fuel resistance||GR I - UL44|
|Oil resistance||UIC 895 OR|
|Rodent protection||Corrugated aluminium tape|
|Maximum operating temperature||90°C|
|Overload maximum core temperature||130°C|
|Short-circuit max. conductor temperature||250°C|
|See all products|