N2XCY 0,6/1 kV FB 3C + 3G (VFD); NC+ST; Sheath: Anti-flame PVC
In factories, substations or power plants. Application as power and control cable in VFD.
StandardsInternational : IEC 60228; IEC 60332-1-2; IEC 60502-1; IEC 60754-1; UIC 895
National : CSA C22.2 N° 131; NTP-IEC 60228; NTP-IEC 60502-1; SAE J-1127; UL 2556; UL 44
In factories, substations or power plants where there is a lot of electrical noise or transiet, for control. measuring or signaling systems, for connection between the variable frequency drive (VFD) and the motor; reduce to electromagnetic interferences.
1. Conductor: Flexible soft copper, class 5.
2. Insulation: Cross linked polyethylene XLPE.
3. 03 insulated grounding conductors: Flexible soft copper, class 5 - XLPE.
4. Inner covering: Anti-flame compound polyvinyl chloride PVC.
5. Concentric conductor: Copper wires + Shield static (overlapped copper tape).
6. Outer sheath: Anti-flame compound polyvinyl chloride PVC.
Excellent properties against heat aging. Resistance to abrasion, moisture and sunlight. Resistance to liquid fuels and oils according to UIC 895 OR. Adequate shielding to transients. Resistance to sulfuric acid according to SAE J1127. Low halogen content according to IEC 60754-1. Low emission of acid gases, less than 14% by weight of the non-metallic component, according to CSA 22.2 N°131 - AG14. Resistant to gasoline GR I according to UL 44. Flame retardant.
From 16 mm2 up to 500 mm2.
INDECO S.A N2XCY 0,6/1 kV - (Nbcores x section) + (Nbcores x grounding cond. section) + conc. cond. section - FB -Year - Sequential length.
Non returnable wooden reels.
Insulation: Black, white, red or black,blue, brown and yellow/green (grounding conductor).
Outer sheath: Black.
NTP-IEC 60228: Conductors of insulated cables.
NTP-IEC 60502-1: Power cables with extruded insulation and their accessories for rated voltages from 1 kV and 3 kV.
IEC 60228: Conductors of insulated cables.
IEC 60502-1: Power cables with extruded insulation and their accesories for rated voltages from 1 kV and 3 kV.
IEC 60332-1-2: Test for vertical flame propagation for a single insulated wire or cable - Procedure for 1 kW pre-mixed flame.
UL 2556: Wire and Cable Test Methods. Section 9.3: FT1 (Vertical-Specimen) Flame Test.
IEC 60754-1: Test on gases evolved during combustion of materials from cables - Part 1: Determination of the halogen acid gas content.
CSA C22.2 N°131 - AG14: Product rating for acid gas compliance.
SAE J1127: Standard for Vehicle Cables. Battery cable Clause 6.7 (Compatibility of fluids) - Resistance to Sulfuric Acid.
UL 44: Thermoset-Insulated Wires and Cables. Section 5.17: Gasoline and oil resistance.
UIC 895 OR: Technical specifications for the supply of insulated electric cables for railway vehicles - Oil resistance.
UL 2556:Wire and Cable Test Methods. Section 220.127.116.11:Carbon-Arc and Xenon-Arc Tests- Sunlight resistance.
|Conductor material||Soft copper|
|Conductor flexibility||Flexible class 5|
|Inner sheath||Flame retardant PVC|
|Concentric conductor||Copper wires and helical copper tape|
|Outer sheath||Flame retardant PVC|
|Rated Voltage Uo/U (Um)||0.6/1 kV|
|Dielectric strength core to screen DC, min.||3.5kV|
|Time of application Dielectric strength core to screen DC||5min.|
|Slightly halogenous||CSA 22.2 AG14 HCl < 14 %|
|U.V resistance||UL 2556 - Sunlight Resistance|
|Electro magnetic interference resistance||Yes|
|Oil resistance||UIC 895 OR|
|Flame retardant||IEC 60332-1-2; FT1|
|Fuel resistance||GR I - UL44|
|Maximum operating temperature||90°C|
|Overload maximum core temperature||130°C|
|Short-circuit max. conductor temperature||250°C|
|See all products|