NA2XS2Y(F) 35 kV PH; NRF-024-CFE; NMX-J-142-ANCE; Outer sheath: HDPE; UV Resist.
Power distribution in medium voltage.
StandardsInternational : IEC 60332-1-2; IEC 60684-2; IEC 60754-1; IEC 60754-2; IEC 61034-2
National : ASTM B 231; ICEA S-93-639; UL 2556
Power distribution in medium voltage. As transformer feeders in substations. In power plants, industrial and operation installations, in residential areas and mining installations, in dry or wet locations.
1. Conductor: Compact stranded aluminium 1350, class B.
2. Inner semi-conductor: Extruded.
3. Insulation: Cross linked polyethylene XLPE-TR (tree retardant).
4. External semi-conductor: Extruded strippable.
These last three components extruded CV (continuous vulcanization) triple extrusion in dry cure process.
5. Screen: Copper wires, according to standard NRF-024-CFE (longitudinally watertight under and over the screen).
6. Outer sheath: High density polyethylene HDPE-UV.
Excellent properties against heat aging. With longitudinally watertight under and over the screen. Resistance to abrasion, moisture and sunlight. Adequate resistance to greases and oils. Low emission of dense smoke and halogen free. Flame retardant.
From 4/0 AWG up to 1250 kcmil
INDECO S.A. NA2XS2Y(F) 35 kV - Gauge - PH (Screen section) - Year - Sequential length.
Non returnable wooden reels.
Outer sheath: Black with red stripes-UV.
ASTM B231: Standard Specification for Concentric-Lay-Stranded Aluminum 1350 Conductors.
NMX-J-142/1-ANCE: Wires and cables - Shielded power cables, rated 5 kV through 35 kV, cross-linked polyethylene or ethylene - propylene rubber insulated - specifications and test methods.
NRF-024-CFE: Single- core power cables rated 5 kV through 35 kV.
IEC 60332-1-2: Test for vertical flame propagation for a single insulated wire or cable - Procedure for 1 kW pre-mixed flame.
UL 2556: Wire and Cable Test Methods. Section 9.3: FT1 (Vertical-Specimen) Flame Test.
IEC 60684-2: Flexible insulating sleeving - Part 2: Methods of test.
IEC 60754-1: Test on gases evolved during combustion of materials from cables. Part 1: Determination of the halogen acid gas content.
IEC 60754-2: Test on gases evolved during combustion of materials from cables. Part 2: Determination of acidity (by pH measurement) and conductivity.
IEC 61034-2: Measurement of smoke density of cables burning under defined conditions.
ICEA S-93-639: 5-46 kV Shielded Power Cable for Use in the Transmission and Distribution of Electric Energy. Section 9.4.2: Oil Immersion Test.
UL 2556: Wire and Cable Test Methods. Section 18.104.22.168: Carbon-Arc and Xenon-Arc Tests- Sunlight resistance.
|Conductor material||aluminum Alloy 1350|
|Material of the inner semi-conductor||Extruded|
|Material of the external semi-conductor||Extruded strippable|
|Sheath colour||Black with red stripes|
|Halogen free||IEC 60754-1|
|Dielectric strength core to screen DC, min.||69.0kV|
|Time of application Dielectric strength core to screen DC||5min.|
|Voltage for partial discharge test||69.0kV|
|Maximal partial discharge test||5pC|
|Longitudinal water tightness||Yes|
|U.V resistance||UL 2556 - Sunlight Resistance|
|Oil resistance||ICEA S-93-639|
|Gases toxicity||Low toxicity to IEC 60684-2|
|Gases corrosivity||Low pH Corrosivity IEC 60754-2|
|Smoke density||IEC 61034-2|
|Flame retardant||IEC 60332-1-2; FT1|
|Maximum operating temperature||90°C|
|Overload maximum core temperature||130°C|
|Short-circuit max. conductor temperature||250°C|
|See all products|