NGY 0,6/1 kV FB Multi-core with ground. cond.; EN 50267-2-1
General use as power cable in low voltage, for fixed installations.
StandardsInternational : EN 50267-2-1; IEC 60228; IEC 60332-1-2; IEC 60502-1
National : NTP-IEC 60228; NTP-IEC 60502-1; UL 2556
General application as power cable. In low voltage distribution power networks, industrial installations, in buildings and operation stations. In fixed installations, indoor and outdoor areas (trays, gutters, staples). It can be installed in ducts, in dry or wet locations.
1. Conductor: Flexible soft copper, class 5.
2. Insulation: HEPR.
3. Insulated grounding conductor: Flexible soft copper, class 5 - HEPR.
4. Filler: Anti-flame compound polyvinyl chloride PVC (when applicable).
5. Outer sheath: Anti-flame compound polyvinyl chloride PVC.
Excellent properties against aging by heat. The outer sheath have the following characteristics: Adequate resistance to greases, oils and abrasion. Flame retardant, low emission of dense smoke, low halogen content according to EN 50267-2-1.
From 1,5 mm2 up to 70 mm2.
INDECO S.A. NGY 0,6/1 kV - (Nb. Cores x Cross Section + Cross Section Ground. Cond.) - FB - Year - Sequential length.
Non returnable wooden reels.
Insulation: See core identification.
Outer sheath: Gray.
NTP-IEC 60228: Conductors of insulated cables.
NTP-IEC 60502-1: Power cables with extruded insulation and their accessories for rated voltages from 1 kV and 3 kV.
IEC 60228: Conductors of insulated cables.
IEC 60502-1: Power cables with extruded insulation and their accessories for rated voltages from 1 kV and 3 kV.
EN 50267-2-1: Common test methods for cables under fire conditions - Tests on gases evolved during combustion of materials from cables. Part 2-1: Procedures - Determination of the amount of halogen acid gas.
IEC 60332-1-2: Test for vertical flame propagation for a single insulated wire or cable - Procedure for 1 kW pre-mixed flame.
UL 2556: Wire and Cable Test Methods. Section 9.3: FT1 (Vertical-Specimen) Flame Test.
|Conductor material||Soft copper|
|Conductor flexibility||Flexible class 5|
|Outer sheath||Flame retardant PVC|
|Rated Voltage Uo/U (Um)||0.6/1 kV|
|Time of application Dielectric strength core to screen DC||5min.|
|Flame retardant||IEC 60332-1-2; FT1|
|Maximum operating temperature||90°C|
|Overload maximum core temperature||130°C|
|Short-circuit max. conductor temperature||250°C|
|See all products|
Products and services
Docs and info
Number of cores
Black + (yellow/green)
Brown + black + (yellow/green)
(Blue or gray) + brown + black + (yellow/green)
Blue + brown + black + grey + (yellow/green)