N2XRY-C 0.6/1 kV with grounding conductor; IEC 60332-3-22 Cat. A
In factories, for control systems.
StandardsInternational : IEC 60228; IEC 60332-1-2; IEC 60332-3-22 Cat.A; IEC 60502-1; IEC 60754-1; UIC 895
National : NTP-IEC 60228; NTP-IEC 60502-1; SAE J-1127; UL 2556; UL 44
In factories, for motor control, lighting, signaling systems and overal equipment interconnection, where mechanical strength is required.
1. Conductor: Soft copper, class 2.
2. Insulation: Anti-flame cross linked polyethylene XLPE.
3. Insulated grounding conductor: Soft copper, class 2 - Anti-flame XLPE.
4. Inner covering: Compound polyvinyl chloride PVC.
5. Armor: Galvanized steel wires.
6. Tape: Polyester tape.
7. Outer sheath: Anti-flame Anti-termite compound polyvinyl chloride PVC.
Good electrical and mechanical properties. Its armor provides additional mechanical protection. Resistance to abrasion and sunlight. Low halogen content according to IEC 60754-1. Resistance to sulfuric acid according to SAE J1127. Resistance to combustible liquids and oils according to UIC 895 OR and Gasoline Resistant GR I according to UL 44. Fire retardant according to IEC 60332-3-22 CAT A.
INDECO S.A N2XRY-C 0,6/1 kV - (Nb. Conductors x Section + Ground Section) - Year - Sequential length.
Non returnable wooden reels.
Insulation: Cores: black with white numbers. Ground: yellow/green.
Outer sheath: Black.
NTP-IEC 60228: Conductors of insulated cables.
NTP-IEC 60502-1: Power cables with extruded insulation and their accessories for rated voltages from 1 kV and 3 kV.
IEC 60228: Conductors of insulated cables.
IEC 60502-1: Power cables with extruded insulation and their accesories for rated voltages of 1 kV and 3 kV.
IEC 60332-1-2: Test for vertical flame propagation for a single insulated wire or cable - Procedure for 1 kW pre-mixed flame.
UL 2556: Wire and Cable Test Methods. Section 9.3: FT1 (Vertical-Specimen) Flame Test.
IEC 60332-3-22: Test for vertical flame spread of vertically-mounted bunched wires or cables - Category A.
IEC 60754-1: Test on gases evolved during combustion of materials from cables - Part 1: Determination of the halogen acid gas content.
SAE J1127: Standard for Vehicle Cables. Battery cable Clause 6.7 (Compatibility of fluids) - Resistance to Sulfuric Acid.
UL 44: Thermoset-Insulated Wires and Cables. Section 5.17: Gasoline and oil resistance.
UIC 895 OR: Technical specifications for the supply of insulated electric cables for railway vehicles - Oil resistance.
UL 2556:Wire and Cable Test Methods. Section 188.8.131.52:Carbon-Arc and Xenon-Arc Tests- Sunlight resistance.
|Conductor material||Soft copper|
|Insulating material||Flame retardant XLPE|
|Core identification||Black cores with white numbers|
|Armour type||Galvanized steel wires|
|Outer sheath||Flame retardant Antitermite PVC|
|Rated Voltage Uo/U (Um)||0.6/1 kV|
|Time of application Dielectric strength core to screen DC||5min.|
|Mechanical resistance to impacts||Good|
|Slightly halogenous||IEC 60754-1|
|U.V resistance||UL 2556 - Sunlight Resistance|
|Oil resistance||UIC 895 OR|
|Flame retardant||IEC 60332-1-2; FT1|
|Fire retardant||IEC 60332-3-22 Cat.A|
|Fuel resistance||GR I - UL44|
|Maximum operating temperature||90°C|
|Overload maximum core temperature||130°C|
|Short-circuit max. conductor temperature||250°C|
|See all products|
Products and services
Docs and info
Wire diameter (mm)