FREETOX NA2XSEOHROH 8.7/15 kV; with bare ground. cond.; for instalation in vertical drilling mines; UV Res.
Power distribution in medium voltage.
StandardsInternational : IEC 60228; IEC 60332-1-2; IEC 60332-3-24 Cat.C; IEC 60502-2; IEC 60684-2; IEC 60754-1; IEC 60754-2; IEC 61034-2
National : ICEA S-93-639; NTP-IEC 60228; NTP-IEC 60502-2; UL 2556
Power distribution in medium voltage, direct application in places with public attendance high where high mechanical strength is required, for instalation in vertical drilling mines.
1. Conductor: Compact stranded aluminium 1350, class 2.
2. Inner semi-conductor: Extruded.
3. Insulation: Cross linked polyethylene XLPE-TR (Tree retardant).
4. External semi-conductor: Extruded strippable.
These last three components extruded CV (continuous vulcanization) triple extrusion.
5. Individual screen: Copper tapes.
6. Grounding conductor: Compact soft copper, class 2.
7. Separation sheath: HFFR halogen free thermoplastic compound.
8. Layer armour: Two Layers of Galvanized steel wires.
9. Tape: Polyester.
10. Outer sheath: HFFR-UV halogen free thermoplastic compound.
Its armour provides additional mechanical protection. The separation sheath and outer sheath have the following characteristics: Fire retardant, low emission dense smoke and halogen free. Adequate resistance to oils. Resistant to sunlight
INDECO S.A. FREETOX NA2XSEOHROH 8,7/15 kV - Nb.cores x section + Ground.cond.Sect. - Year - Sequential length.
Non returnable wooden reels.
Insulation: Natural (Cores are identified with binder tapes; colour: white, black, red)
Outer sheath: Red-UV.
NTP-IEC 60228: Conductors of insulated cables.
NTP-IEC 60502-2: Power cables with extruded insulation and their accessories for rated voltages from 6 kV up to 30 kV.
IEC 60228: Conductors of insulated cables.
IEC 60502-2: Power cables with extruded insulation and their accessories for rated voltages from 6 kV up to 30 kV.
IEC 60332-1-2: Test for vertical flame propagation for a single insulated wire or cable - Procedure for 1 kW pre-mixed flame.
IEC 60332-3-24: Test for vertical flame spread of vertically-mounted bunched wires or cables - Category C.
IEC 60684-2: Flexible insulating sleeving - Part 2: Methods of test.
IEC 60754-1: Test on gases evolved during combustion of materials from cables - Part 1: Determination of the halogen acid gas content.
IEC 60754-2: Test on gases evolved during combustion of materials from cables - Part 2: Determination of acidity (by pH measurement) and conductivity.
IEC 61034-2: Measurement of smoke density of cables burning under defined conditions.
ICEA S-93-639: 5-46kV Shielded Power Cable for Use in the Transmission and Distribution of Electric Energy. Section 9.4.2: Oil inmersion test.
UL 2556: Wire and Cable Test Methods. Section 184.108.40.206: Carbon-Arc and Xenon-Arc Tests- Sunlight resistance.
|Conductor material||Aluminum Alloy 1350|
|Material of the inner semi-conductor||Extruded|
|Material of the external semi-conductor||Extruded strippable|
|Individual screen||Copper tapes helically applied|
|Armour type||Galvanized steel wires|
|Outer sheath||Halogen free thermoplastic compound - UV Resist.|
|Halogen free||IEC 60754-1|
|Sheath colour||Red - UV|
|Dielectric strength core to screen DC, min.||30.5kV|
|Time of application Dielectric strength core to screen DC||5min.|
|Voltage for partial discharge test||15.0kV|
|Maximal partial discharge test||10pC|
|Mechanical resistance to impacts||Good|
|U.V resistance||UL 2556 - Sunlight Resistance|
|Oil resistance||ICEA S-93-639|
|Gases corrosivity||Low pH Corrosivity IEC 60754-2|
|Gases toxicity||Low toxicity to IEC 60684-2|
|Smoke density||IEC 61034-2|
|Fire retardant||IEC 60332-3-24 Cat.C|
|Flame retardant||IEC 60332-1-2; FT1|
|Max. conductor temperature in service||90°C|
|Overload maximum core temperature||130°C|
|Short-circuit max. conductor temperature||250°C|
|See all products|
Products and services
Docs and info
Wire diameter (mm)
Conditions for installation in vertical drilling mines