N2XBY 600 V; 8000 series Aluminium; Multicore with ground. cond.
General application as power cable in low voltage.
StandardsInternational : IEC 60332-1-2
National : ASTM B 801; ICEA S-95-658; UL 2556
General application as power cable. In low voltage distribution power networks, industrial installations, in buildings and operating stations, indoor and outdoor areas. It can be installed in ducts, in dry or wet locations where mechanical strength is requiered.
1. Conductor: Compact 8000 series Aluminium, class B.
2. Insulation: Cross linked polyethylene XLPE.
3. Insulated grounding conductor: Compact 8000 series Aluminium, class B - XLPE.
3. Inner covering: Compound polyvinyl chloride PVC.
4. Armour: Galvanized steel tapes.
5. Outer sheath: Compound polyvinyl chloride PVC.
Good electrical and mechanical properties. Cross-linked polyethylene insulation allows greater power capacity under any operation condition, minimum dilectric losses, high insulation resistance. Its armour provides additional mechanical protection. The PVC outer sheath allows an adequate resistance to greases, oils, abrasion and sunlight. Flame retardant.
INDECO S.A NA2XBY 600 V - (Nb. cores x Gauge + Grounding cond. section) - Year - Sequential length.
Non returnable wooden reels.
Insulation: See core identification.
Outer sheath: Black.
ASTM B 801: Standard Specification for Concentric-Lay-Stranded Conductors of 8000 series Aluminum Alloy for subsequent covering or Insulation.
ICEA S-95-658: Power cables rated 200 volts or less for the distribution of electrical energy.
IEC 60332-1-2: Test for vertical flame propagation for a single insulated wire or cable - Procedure for 1 kW pre-mixed flame.
UL 2556: Wire and Cable Test Methods. Section 9.3: FT1 (Vertical-Specimen) Flame Test.
UL 2556: Wire and Cable Test Methods. Section 18.104.22.168: Carbon-Arc and Xenon-Arc Tests- Sunlight resistance.
|Conductor material||Aluminum 8000 series|
|Armour type||Steel tapes|
|Time of application Dielectric strength core to screen DC||5min.|
|Mechanical resistance to impacts||Good|
|U.V resistance||UL 2556 - Sunlight Resistance|
|Flame retardant||IEC 60332-1-2; FT1|
|Maximum operating temperature||90°C|
|Overload maximum core temperature||130°C|
|Short-circuit max. conductor temperature||250°C|
|See all products|
Products and services
Docs and info
Core Identification L.V with ground cond.
Number of cores
Black + (yellow or green or yellow/green or green/yellow)
White + black, white + red, white + blue, blue + brown, blue + black or black + red + (yellow or green or yellow/green or green/yellow)
White + black + red, black + red + blue, brown + black + grey or blue + brown + black + (yellow or green or yellow/green or green/yellow)
White + black + red + blue, blue + brown + black + grey + (yellow or green or yellow/green or green/yellow)