StandardsInternational : IEC 60332-1-2; IEC 60332-3-24 Cat.C; IEC 60684-2; IEC 60754-1; IEC 60754-2; IEC 61034-2
National : ASTM B 231; ICEA S-93-639; ICEA S-94-649; UL 2556
Power distribution in medium voltage, direct application in places with public attendance high. Not recommended for outdoor installations.
1. Conductor: Compact stranded 1350 aluminium, class B.
2. Inner semi-conductor: Extruded.
3. Insulation: Cross linked polyethylene XLPE-TR (Tree retardant).
4. External semi-conductor: Extruded strippable.
These last three components extruded CV (continuous vulcanization) triple extrusion in dry cure process.
5. Concentric conductor: Copper wires helically applied with 100% for concentric neutral according to ICEA S-94-649 + copper tape in open spiral (longitudinally watertight under and over concentric conductor).
6. Outer sheath: HFFR halogen-free thermoplastic compound.
Excellent properties against heat aging. Insulation level of 133%. Longitudinally watertight under and over concentric conductor. The outer sheath has the following characteristics: Fire retardant, low emission dense smoke and halogen free. Adequate resistance to oils.
INDECO S.A. FREETOX NA2XCOH(F) 15 kV - Gauge - NC100 - Year - Sequential length.
Non returnable wooden reels.
Outer sheath: Red.
ASTM B231: Standard specification for concentric-lay-stranded aluminum 1350 conductors.
ICEA S-94-649: Concentric neutral Cables rated 5 through 46 kV.
IEC 60332-1-2: Test for vertical flame propagation for a single insulated wire or cable - Procedure for 1 kW pre-mixed flame.
UL 2556: Wire and Cable Test Methods. Section 9.3: FT1 (Vertical-Specimen) Flame Test.
IEC 60332-3-24: Test for vertical flame spread of vertically-mounted bunched wires or cables - Category C.
IEC 60684-2: Flexible insulating sleeving - Part 2: Methods of test.
IEC 60754-1: Test on gases evolved during combustion of materials from cables - Part 1: Determination of the halogen acid gas content.
IEC 60754-2: Test on gases evolved during combustion of materials from cables - Part 2: Determination of acidity (by pH measurement) and conductivity.
IEC 61034-2: Measurement of smoke density of cables burning under defined conditions.
ICEA S-93-639: 5-46 kV Shielded Power Cable for Use in the Transmission and Distribution of Electric Energy. Section 9.4.2: Oil Immersion Test.
|Conductor material||aluminum Alloy 1350|
|Material of the inner semi-conductor||Extruded|
|Material of the external semi-conductor||Extruded strippable|
|Concentric conductor||Copper wires and helical copper tape|
|Outer sheath||Halogen free thermoplastic compound|
|Halogen free||IEC 60754-1|
|Dielectric strength core to screen DC, min.||35.0kV|
|Time of application Dielectric strength core to screen DC||5min.|
|Voltage for partial discharge test||35.0kV|
|Maximal partial discharge test||5pC|
|Longitudinal water tightness||Yes|
|Oil resistance||ICEA S-93-639|
|Gases toxicity||Low toxicity to IEC 60684-2|
|Gases corrosivity||Low pH Corrosivity IEC 60754-2|
|Smoke density||IEC 61034-2|
|Flame retardant||IEC 60332-1-2; FT1|
|Fire retardant||IEC 60332-3-24 Cat.C|
|Maximum operating temperature||90°C|
|Overload maximum core temperature||130°C|
|Short-circuit max. conductor temperature||250°C|
|See all products|
Products and services
Docs and info
Concentric Neutral Nb of wires