N2XSSAY(F) 15 kV 133% I.L. PH; Anti-rodent; DS ISA REP
Power distribution in medium voltage.
StandardsInternational : IEC 60332-1-2; IEC 60754-1; IEC 61034-2
National : ASTM B 8; ICEA S-93-639; UL 2556
Power distribution in medium voltage. As transformer feeders in substations. In power plants, industrial and operation installations, in residential areas and mining installations, in dry or wet locations.
1. Conductor: Compact soft copper, class B.
2. Inner semi-conductor: Extruded compound.
3. Insulation: Cross linked polyethylene XLPE-TR (Tree retardant).
4. External semi-conductor: Extruded strippable.
These last three components extruded CV (continuous vulcanization) triple extrusion in dry cure process.
5. Screen: Copper wires (with longitudinally watertight under and over the screen).
6. Radial watertight: Single-ply aluminium tape.
7. Outer sheath: Anti-rodent low smoke - low halogen compound polyvinyl chloride PVC.
Excellent properties against heat aging. To 133% for insulation level. Longitudinally watertight under and over the screen; radial watertight under the outer sheath. Resistance to abrasion, moisture and sunlight. Adequate resistance to grease, oils, abrasion and sunlight. Flame retardant. Low emission of dense smoke and halogens. Resistance to attack by rodents.
INDECO S.A. N2XSSAY(F) 15 kV 133% I.L. - Gauge - PH - Year - Sequential length.
Non returnable wooden reels.
Outer sheath: Black.
ASTM B8: Concentric-Lay-Stranded copper conductors, hard, medium-hard, or soft.
ICEA S-93-639: 5 - 46 kV Shielded Power Cable for use in the transmission and distribution of electric energy.
IEC 60332-1-2: Test for vertical flame propagation for a single insulated wire or cable - Procedure for 1 kW pre-mixed flame.
UL 2556: Wire and Cable Test Methods. Section 9.3: FT1 (Vertical-Specimen) Flame Test.
IEC 60754-1: Test on gases evolved during combustion of materials from cables - Part 1: Determination of the halogen acid gas content.
IEC 61034-2: Measurement of smoke density of cables burning under defined conditions.
UL 2556: Wire and Cable Test Methods. Section 18.104.22.168: Carbon-Arc and Xenon-Arc Tests- Sunlight resistance.
|Conductor material||Soft copper|
|Material of the inner semi-conductor||Extruded|
|Material of the external semi-conductor||Extruded strippable|
|Outer sheath||PVC LS-LH-Antirodent|
|Dielectric strength core to screen DC, min.||44.0kV|
|Time of application Dielectric strength core to screen DC||5min.|
|Voltage for partial discharge test||44.0kV|
|Maximal partial discharge test||5pC|
|Longitudinal water tightness||Yes|
|Radial water tightness||Yes|
|Rodent protection||ARS (Anti rodent sheath)|
|Slightly halogenous||IEC 60754-1|
|Smoke density||IEC 61034-2|
|U.V resistance||UL 2556 - Sunlight Resistance|
|Flame retardant||IEC 60332-1-2; FT1|
|Maximum operating temperature||90°C|
|Overload maximum core temperature||130°C|
|Short-circuit max. conductor temperature||250°C|
|See all products|
Products and services
Docs and info
Ampacity in buried duct
Conductor Gauge (AWG/kcmil)
Ampacity - buried in duct; 20 °C (A)