CU/XLPE/PC/LSZH 0,6/1 kV FB Multicore; ANSALDO
In factories, substations or power plants.
StandardsInternational : IEC 60228; IEC 60331; IEC 60331-21 ; IEC 60332-3-24 Cat.C; IEC 60502-1; IEC 60684-2; IEC 60754-1; IEC 60754-2; IEC 60811-401; IEC 60811-402; IEC 60811-501; IEC 60811-502; IEC 60811-504; IEC 60811-505; IEC 60811-506; IEC 60811-507; IEC 60811-508; IEC 61034-2
National : ICEA S-95-658
In factories, substations or power plants where there is a lot of electrical noise or transient, for control, measuring or signaling systems. Direct application in places with public attendance high. Not recommended for outdoor installations.
1. Conductor: Flexible soft copper, class 5.
2. Flame Barrier: Mica tape.
3. Insulation: Cross linked polyethylene XLPE.
4. Tape: Poliester.
5. Screen: Copper tape covered with plastic adhesive tape on one side.
- Application: Helical.
- Percentage of coverage: 100%.
- Thickness of tape: 0.064 mm.
- Overlap: 15%.
6. Drain conductor: Tinned copper wire.
7. Outer sheath: HFFR halogen free thermoplastic compound.
Minimum dielectric losses, high insulation resistant. Flame resistant. Adequate transient shield. The outer sheath has the following characteristics: Fire retardant, low emission dense smoke and halogen free.
INDECO S.A. CU/MGT/XLPE/SCR/LSZH 0,6/(1,2) kV - Nro of cores x Section - IEC 60502-1 IEC 60332-3-24 IEC 61034 IEC 60754 IEC 60331-1 -Year - Sequential length.
Non returnable wooden reels.
Insulation: See core identification.
Outer sheath: Black.
IEC 60228: Conductors of insulated cables.
IEC 60502-1: Power cables with extruded insulation and their accessories for rated voltages from 1 kV and 3 kV.
IEC 60331-1: Tests for electric cables under fire conditions. Test method for fire with shock at a temperature of at least 830 °C for cables of rated voltage up to and including 0,6/1,0 kV and with an overall diameter exceeding 20 mm.
IEC 60331-21: Tests for electric cables under fire conditions. Procedures and requirements - Cables of rated voltage up to and including 0,6/1 kV.
IEC 60332-3-24: Test for vertical flame spread of vertically-mounted bunched wires or cables - Category C.
IEC 60684-2: Flexible insulating sleeving - Part 2: Methods of test.
IEC 60754-1: Test on gases evolved during combustion of materials from cables - Part 1: Determination of the halogen acid gas content.
IEC 60754-2: Test on gases evolved during combustion of materials from cables - Part 2: Determination of acidity (by pH measurement) and conductivity.
IEC 61034-2: Measurement of smoke density of cables burning under defined conditions.
ICEA S-95-658: Power cables rated 2000 volts or less for the distribution of electrical energy. Section 6.4.2: Oil Immersion Test.
|Conductor material||Soft copper|
|Conductor flexibility||Flexible class 5|
|Electrostatic shielding||Copper tapes helically applied|
|Outer sheath||Halogen free thermoplastic compound|
|Halogen free||IEC 60754-1|
|Dielectric strength core to screen DC, min.||3.5kV|
|Time of application Dielectric strength core to screen DC||5min.|
|Oil resistance||ICEA S-95-658|
|Gases toxicity||Low toxicity to IEC 60684-2|
|Gases corrosivity||Low pH Corrosivity IEC 60754-2|
|Smoke density||IEC 61034-2|
|Fire resistant||IEC 60331-1|
|Fire retardant||IEC 60332-3-24 Cat.C|
|Bending factor when installed||6(xD)|
|Maximum operating temperature||90°C|
|Overload maximum core temperature||130°C|
|Short-circuit max. conductor temperature||250°C|
|See all products|
Products and services
Docs and info
Core Identification L.V
Number of cores
Black cores printed with white numbers from 1 to 5
Black cores printed with white numbers from 1 to 7
Black cores printed with white numbers from 1 to 12