CAAI 1,1 kV Covered Neutral AAAC with Public Lighting
For overhead secundary distribution networks.
StandardsInternational : IEC 60228; IEC 60811-201; IEC 60811-401; IEC 60811-402; IEC 60811-501; IEC 60811-502; IEC 60811-507; IEC 60811-511
National : IRAM 2263; NTP-IEC 60228
For urban and rural overhead secundary distribution networks.
1. Conductor: Compact aluminium 1350, class 2.
2. Insulation: Cross linked polyethylene XLPE.
3. Public lighting: Compact auminium 1350 insulated with cross-linked polyethylene XLPE.
4. Insulated neutral messenger: AAAC - All Alloy Aluminium 6201 - XLPE.
Decreases energy theft, cross-linked polyethylene allows more current capacity and high insulation resistance, lower inductive reactance than with bare conductors, used in overhead distribution lines. Increased safety due to its mechanical strength and toughness of the insulation. Insulators are not necessary for installation. Resistance to abrasion, weather and sunlight.
INDECO S.A. CAAI 1,1 kV - (Nb. Cores x Section) + (Nb. conductors x public light. section) + NA Neutral messen. section - Year - Sequential length.
Non returnable wooden reels.
Black with rib marking.
NTP-IEC 60228: Conductors of insulated cables.
IEC 60228: Conductors of insulated cables.
IRAM 2263: Pre-assembled cables with aluminum conductors, with cross-linked polyethylene (XLPE) insulation for overhead lines up to 1,1 kV.
IEC 60811-201: Measurement of insulation thickness.
IEC 60811-401: Thermal ageing methods -Ageing in an air oven.
IEC 60811-402: Water absorption test.
IEC 60811-501: Test for determining the mechanical properties of insulating and sheating.
IEC 60811-502: Shrinkage test for isolations.
IEC 60811-507: Hot elongation test for crosslinked materials.
IEC 60811-511: Measurement of hot melt index of polyethylene compounds.
|Phase Conductor Type||AAC - All Aluminium Conductor|
|Core identification||Rib markings|
|Neutral messenger||AAAC - All Alloy Aluminium Conductor|
|Time of application Dielectric strength core to screen DC||5min.|
|Bending factor when installed||4(xD)|
|Maximum operating temperature||90°C|
|Overload maximum core temperature||130°C|
|Short-circuit max. conductor temperature||250°C|
|See all products|