N2XSY-C 0,6/1 kV FB; Screen electr. resist. PH+PC: 2,0 Ohm/km; Outer sheath PVC Antiflame/Anti-Rodent
In factories, for systems of control.
StandardsInternational : FT4 IEEE1202 ; IEC 60228; IEC 60332-1-2; IEC 60502-1; IEC 60754-1; UIC 895
National : NTP-IEC 60228; NTP-IEC 60502-1; SAE J-1127; UL 2556; UL 44
In factories, for systems of motor control, lighting, signaling and overal equipment interconnection, control circuits of automatic machines. Ideal for installation in cement ducts.
1. Conductor: Flexible soft copper, class 5.
2. Insulation: Anti-flame cross linked polyethylene XLPE.
3. Inner covering: Anti-flame compound polyvinyl chloride PVC.
4. Screen: Copper wires + copper tape in open spiral.
5. Tape: Polyester.
6. Outer sheath with tearing thread: Anti-flame and anti-rodent compound polyvinyl chloride PVC.
The cross-linked polyethylene insulation allows greater current capacity in any operating condition, minimum dielectric losses, high insulation resistance. It can be installed on a tray (Tray Cable). The outer PVC cover gives it an adequate resistance to abrasion, moisture and sunlight. Resistance to liquid fuels and oils according to UIC 895 OR. Resistance to sulfuric acid according to SAE J1127. Low halogen content according to IEC 60754-1. Resistant to gasoline GR I according to UL 44. Fire retardant according to IEEE 1202/FT-4. Resistance to attack by rodents.
From 1,5 mm2 up to 10 mm2.
INDECO S.A N2XSY-C 0,6/1 kV - N° Conductors x Section - FB - Year - Sequential length.
Non returnable wooden reels.
Insulation: Black with white numbers.
Outer sheath: Black.
NTP-IEC 60228: Conductors of insulated cables.
NPT-IEC 60502-1: Power cables with extruded insulation and their accesories for rated voltages from 1 kV and 3kV.
IEC 60228: Conductors of insulated cables.
IEC 60502-1: Power cables with extruded insulation and their accesories for rated voltages from 1 kV and 3 kV.
IEC 60332-1-2: Test for vertical flame propagation for a single insulated wire or cable - Procedure for 1 kW pre-mixed flame.
UL 2556: Wire and Cable Test Methods. Section 9.3: FT1 (Vertical-Specimen) Flame Test.
FT4/IEEE 1202: Vertical Tray Flame Test.
IEC 60754-1: Test on gases evolved during combustion of materials from cables - Part 1: Determination of the halogen acid gas content.
SAE J1127: Standard for Vehicle Cables. Battery cable Clause 6.7 (Compatibility of fluids) - Resistance to Sulfuric Acid.
UL 44: Thermoset-Insulated Wires and Cables. Section 5.17: Gasoline and oil resistance.
UIC 895 OR: Technical specifications for the supply of insulated electric cables for railway vehicles - Oil resistance.
UL 2556: Wire and Cable Test Methods. Section 22.214.171.124:Carbon-Arc and Xenon-Arc Tests- Sunlight resistance.
|Conductor material||Soft copper|
|Conductor flexibility||Flexible class 5|
|Insulating material||Flame retardant XLPE|
|Core identification||Black cores with white numbers|
|Screen||Copper wire + copper tape|
|Outer sheath||Flame retardant Anti-rodent PVC|
|Resistance of the screen||2.0Ohm/km|
|Dielectric strength core to screen DC, min.||3.5kV|
|Time of application Dielectric strength core to screen DC||5min.|
|Electro magnetic interference resistance||Yes|
|Rodent protection||ARS (Anti rodent sheath)|
|Slightly halogenous||IEC 60754-1|
|U.V resistance||UL 2556 - Sunlight Resistance|
|Flame retardant||IEC 60332-1-2; FT1|
|Fire retardant||FT4/IEEE 1202|
|Oil resistance||UIC 895 OR|
|Fuel resistance||GR I - UL44|
|Maximum operating temperature||90°C|
|Overload maximum core temperature||130°C|
|Short-circuit max. conductor temperature||250°C|
|See all products|