FREETOX N2XOH 600 V Multi-core with Insulated grounding conductor; UV. Resist.
Special application in places with poor ventilation and high public attendance.
StandardsInternational : IEC 60332-1-2; IEC 60332-3-24 Cat.C; IEC 60684-2; IEC 60754-1; IEC 60754-2; IEC 61034-2
National : ASTM B 8; ICEA S-95-658; UL 2556
In low voltage power distribution networks. Special application in places with poor ventilation and high public attendance. It can be installed in ducts or in dry, damp and wet environments.
1. Conductor: Compact soft copper, class B.
2. Insulation: Cross linked polyethylene XLPE.
3. Insulated grounding conductor: Soft copper, class B - XLPE.
4. Outer sheath: HFFR-UV halogen free thermoplastic compound..
The cable has excellent electrical properties. The cross-linked polyethylene insulation allows a higher power current capacity under any operation conditions, lower dielectric losses and high insulation resistance. The outer sheath have the following characteristics: Fire retardant, low emission of dense smoke and halogen free. Resistance to sunlight. Adequate resistance to oil.
From 8 AWG up to 4/0 AWG.
INDECO S.A. FREETOX N2XOH 600 V - Nb Cores x Gauge + Grounding Cond. Gauge - Year - Sequential length.
Non returnable wooden reels.
Insulation: See Core identification.
Outer sheath: Black-UV.
ASTM B8: Concentric-lay-stranded copper conductors, hard, medium-hard, or soft.
ICEA S-95-658: Power cables rated 2000 volts or less for the distribution of electrical energy.
IEC 60332-1-2: Test for vertical flame propagation for a single insulated wire or cable - Procedure for 1 kW pre-mixed flame.
UL 2556: Wire and Cable Test Methods. Section 9.3: FT1 (Vertical-Specimen) Flame Test.
IEC 60332-3-24: Test for vertical flame spread of vertically-mounted bunched wires or cables - Category C.
IEC 60684-2: Flexible insulating sleeving - Part 2: Methods of test.
IEC 60754-1: Test on gases evolved during combustion of materials from cables - Part 1: Determination of the halogen acid gas content.
IEC 60754-2: Test on gases evolved during combustion of materials from cables - Part 2: Determination of acidity (by pH measurement) and conductivity.
IEC 61034-2: Measurement of smoke density of cables burning under defined conditions.
ICEA S-95-658: Power cables rated 2000 volts or less for the distribution of electrical energy. Section 6.4.2: Oil Immersion Test.
UL 2556: Wire and Cable Test Methods. Section 126.96.36.199: Carbon-Arc and Xenon-Arc Tests- Sunlight resistance.
|Conductor material||Soft copper|
|Outer sheath||Halogen free thermoplastic compound - UV Resist.|
|Sheath colour||Black - UV|
|Halogen free||IEC 60754-1|
|Cable flexibility||Class B ASTM B8|
|U.V resistance||UL 2556 - Sunlight Resistance|
|Gases toxicity||Low toxicity to IEC 60684-2|
|Gases corrosivity||Low pH Corrosivity IEC 60754-2|
|Oil resistance||ICEA S-95-658|
|Smoke density||IEC 61034-2|
|Fire retardant||IEC 60332-3-24 Cat.C|
|Flame retardant||IEC 60332-1-2; FT1|
|Maximum operating temperature||90°C|
|Overload maximum core temperature||130°C|
|Short-circuit max. conductor temperature||250°C|
|See all products|
Products and services
Docs and info
Core Identification L.V with ground cond.
Number of cores
White + black + Grounding conductor (Green)
Blue + black + red + Grounding conductor (Green)
Blue + black + red + white + Grounding conductor (Green)