NA2XR2Y 5 kV; 8000 series Alum.; Unshield Multicore with isolated ground. cond.; Outer sheath: HDPE; UV Resist.
General application as power cable in low voltage.
StandardsInternational : IEC 60332-1-2; IEC 60684-2; IEC 60754-1; IEC 60754-2; IEC 61034-2
National : ASTM B 801; ICEA S-95-658; ICEA S-96-659; UL 2556
Power distribution in low voltage. As transformer feeders in substations. In power plants, industrial and operation installations, in residential areas and mining installations, in dry locations or underwater (submerged) where mechanical strength is required.
1. Conductor: Compacted aluminium 8000 series, class B.
2. Inner semi-conductor: Extruded.
3. Insulation:Cross linked polyethylene XLPE-TR (Tree retardant).
4. Insulated grounding conductor: Soft copper, class B - XLPE.
5. Inner covering: Anti-flame compound polyvinyl chloride PVC.
6. Armor: Galvanized steel wires with HDPE-UV.
7. Tape: Polyester.
8. Outer sheath: High density polyethylene HDPE-UV.
Excellent properties against heat aging. The HDPE cover over each armor wire provides protection from contact with saline water. The outer sheath has the following characteristics: low emission dense smoke and halogen free. Resistance to abrasion, moisture and sunlight. Adequate resistance to greases and oils. Flame retardant.
INDECO S.A. NA2XR2Y 5 kV - (Nb Cores x Gauge + Ground. cond. gauge) - Year - Sequential length.
Non returnable wooden reels.
Insulation: White, black and red. grounding conductor: Green.
Outer sheath: Black with yellow stripes.
ASTM B 801: Standard Specification for Concentric-Lay-Stranded Conductors of 8000 series Aluminum Alloy for subsequent covering or Insulation.
ICEA S-96-659: Nonshielded Cables Rated 2001-5000 V for Use in the Distribution of Electric Energy.
IEC 60332-1-2: Test for vertical flame propagation for a single insulated wire or cable - Procedure for 1 kW pre-mixed flame.
UL 2556: Wire and Cable Test Methods. Section 9.3: FT1 (Vertical-Specimen) Flame Test.
IEC 60684-2: Flexible insulating sleeving - Part 2: Methods of test.
IEC 60754-1: Test on gases evolved during combustion of materials from cables. Part 1: Determination of the halogen acid gas content.
IEC 60754-2: Test on gases evolved during combustion of materials from cables. Part 2: Determination of acidity (by pH measurement) and conductivity.
IEC 61034-2: Measurement of smoke density of cables burning under defined conditions.
ICEA S-95-658: Power cables rated 2000 volts or less for the distribution of electrical energy. Section 6.4.2: Oil Immersion Test.
UL 2556: Wire and Cable Test Methods. Section 22.214.171.124: Carbon-Arc and Xenon-Arc Tests- Sunlight resistance.
|Conductor material||Aluminum 8000 series|
|Inner sheath||Flame retardant PVC|
|Armour type||Galvanized steel wires with HDPE-UV sheath|
|Sheath colour||Black with 3 longitudinal lines|
|Halogen free||IEC 60754-1|
|Time of application Dielectric strength core to screen DC||5min.|
|Mechanical resistance to impacts||Good|
|U.V resistance||UL 2556 - Sunlight Resistance|
|Oil resistance||ICEA S-95-658|
|Gases toxicity||Low toxicity to IEC 60684-2|
|Gases corrosivity||Low pH Corrosivity IEC 60754-2|
|Smoke density||IEC 61034-2|
|Flame retardant||IEC 60332-1-2; FT1|
|Maximum operating temperature||90°C|
|Overload maximum core temperature||130°C|
|Short-circuit max. conductor temperature||250°C|
|See all products|
Products and services
Docs and info
Wire gauge (BWG)