NA2X2Y 0,6/1 kV Single core; GSC002-4
General use as power cable, for fixed installations.
StandardsInternational : IEC 60228; IEC 60332-1-2; IEC 60502-1; IEC 60684-2; IEC 60754-1; IEC 60754-2; IEC 61034-2
National : GSC002; ICEA S-95-658; NTP-IEC 60228; NTP-IEC 60502-1; UL 2556
General application as power cable. In low voltage distribution power networks, industrial installations, in buildings and operation stations. In fixed installations, indoor and outdoor areas (trays, gutters, staples). It can be installed in ducts, in dry or wet locations.
1. Conductor: Compact aluminium 1350, class 2.
2. Insulation: XLPE cross linked polyethylene.
3. Outer sheath: Low Linear Dendsity Polyethylene LLDPE-UV.
Cross-linked polyethylene insulation allows greater power capacity under any operating condition, minimum dielectric losses, high insulation resistance. The outer sheath has the following characteristics: low emission dense smoke and halogen free. Resistance to abrasion, moisture and sunlight. Adequate resistance to greases and oils. Flame restardant.
25 mm2 and 70 mm2.
ENEL DISTRIBUCION PERU INDECO S.A. AL-XLPE-PO 0,6/1(1,2) kV - 1xSection - Month - Year - Sequential length.
Non returnable wooden reels.
Outer sheath: Black-UV.
NTP-IEC 60228: Conductors of insulated cables.
NTP-IEC 60502-1: Power cables with extruded insulation and their accessories for rated voltages from 1 kV and 3 kV.
IEC 60228: Conductors of insulated cables.
IEC 60502-1: Power cables with extruded insulation and their accessories for rated voltages from 1 kV and 3 kV.
GSC002-4: Underground low voltage distribution cables with rated voltage Uo/U(Umax)=0,6/1(1,2)kV.
IEC 60332-1-2: Test for vertical flame propagation for a single insulated wire or cable - Procedure for 1 kW pre-mixed flame.
UL 2556: Wire and Cable Test Methods. Section 9.3: FT1 (Vertical-Specimen) Flame Test.
IEC 60684-2: Flexible insulating sleeving - Part 2: Methods of test.
IEC 60754-1: Test on gases evolved during combustion of materials from cables. Part 1: Determination of the halogen acid gas content.
IEC 60754-2: Test on gases evolved during combustion of materials from cables. Part 2: Determination of acidity (by pH measurement) and conductivity.
IEC 61034-2: Measurement of smoke density of cables burning under defined conditions.
ICEA S-95-658: Power cables rated 2000 volts or less for the distribution of electrical energy. Section 6.4.2: Oil: Oil Immersion Test.
UL 2556: Wire and Cable Test Methods. Section 184.108.40.206: Carbon-Arc and Xenon-Arc Tests- Sunlight resistance.
|Conductor material||aluminum Alloy 1350|
|Sheath colour||Black - UV|
|Halogen free||IEC 60754-1|
|Time of application Dielectric strength core to screen DC||5min.|
|U.V resistance||UL 2556 - Sunlight Resistance|
|Oil resistance||ICEA S-95-658|
|Gases toxicity||Low toxicity to IEC 60684-2|
|Gases corrosivity||Low pH Corrosivity IEC 60754-2|
|Smoke density||IEC 61034-2|
|Flame retardant||IEC 60332-1-2; FT1|
|Maximum operating temperature||90°C|
|Overload maximum core temperature||130°C|
|Short-circuit max. conductor temperature||250°C|
|See all products|