XLPE/LSZH 600 V; QUELLAVECO
Special application in places with poor ventilation and places public attendance high.
StandardsInternational : IEC 60332-1-2; IEC 60332-3-24 Cat.C; IEC 60684-2; IEC 60754-1; IEC 60754-2; IEC 61034-2
National : ASTM B 8; ICEA S-73-532; ICEA S-95-658; UL 2556
In industrial plants, for systems of motor control, lighting, signaling and overal equipment interconnection, control circuits of automatic machines. Direct application in places with public attendance high.
1. Conductor: Soft copper compressed, class B.
2. Insulation: Cross linked polyethylene XLPE.
3. Filler: Halogen free thermoplastic compound.
4. Outer sheath: HFFR-UV Halogen free thermoplastic compound.
The cable has excellent electric properties. The cross-linked polyethylene insulation allows a higher power capacity current under any operation conditions, lower dielectric losses, high insulation resistance. The filler and outer sheath have the following characteristics: Fire retardant, low emission dense smoke and halogen free. Adequate resistance to oils. Resistance to sunnlight.
INDECO S.A XLPE/LSZH 600 V - N° Conductors x Gauge - Year - Sequential length.
Non returnable wooden reels.
Insulation: According to Method 1 Table E2.
Outer sheath: Black.
ASTM B8: Concentric-Lay-Stranded copper conductors, hard, medium-hard, or soft.
ICEA S-73-532: Standard for Control - Thermocouple Extension, and Instrumentation Cables
IEC 60332-1-2: Test for vertical flame propagation for a single insulated wire or cable - Procedure for 1 kW pre-mixed flame.
UL 2556: Wire and Cable Test Methods. Section 9.3: FT1 (Vertical-Specimen) Flame Test.
IEC 60332-3-24: Test for vertical flame spread of vertically-mounted bunched wires or cables - Category C.
IEC 60684-2: Flexible insulating sleeving - Part 2: Methods of test.
IEC 60754-1: Test on gases evolved during combustion of materials from cables - Part 1: Determination of the halogen acid gas content.
IEC 60754-2: Test on gases evolved during combustion of materials from cables - Part 2: Determination of acidity (by pH measurement) and conductivity.
IEC 61034-2: Measurement of smoke density of cables burning under defined conditions.
ICEA S-95-658: Power cables rated 2000 volts or less for the distribution of electrical energy. Section 6.4.2: Oil Immersion Test.
|Conductor material||Soft copper|
|Outer sheath||Halogen free thermoplastic compound - UV Resist.|
|Halogen free||IEC 60754-1|
|Time of application Dielectric strength core to screen DC||5min.|
|Oil resistance||ICEA S-93-639|
|Gases toxicity||Low toxicity to IEC 60684-2|
|Gases corrosivity||Low pH Corrosivity IEC 60754-2|
|Smoke density||IEC 61034-2|
|Flame retardant||IEC 60332-1-2; FT1|
|Fire retardant||IEC 60332-3-24 Cat.C|
|Bending factor when installed||7(xD)|
|Maximum operating temperature||90°C|
|Overload maximum core temperature||130°C|
|Short-circuit max. conductor temperature||250°C|
|See all products|