XLPE/LSZH 600 V; with ground. conductor; QUELLAVECO
Special application in places with poor ventilation and places public attendance high.
StandardsInternational : IEC 60754-1; IEC 60754-2; IEC 61034; NES 713
National : ASTM B 8; ICEA S-95-658
In industrial plants, for systems of motor control, lighting, signaling and overal equipment interconnection, control circuits of automatic machines. Direct application in places with public attendance high.
1. Conductor: Soft copper compressed, class B.
2. Insulation: Cross linked polyethylene XLPE.
3. Insulated grounding conductor: Soft copper, class 2 - Cross linked polyethylene XLPE.
4. Outer sheath: HFFR-UV Halogen free thermoplastic compound.
The cable has excellent electric properties. The cross-linked polyethylene insulation allows a higher power capacity current under any operation conditions, lower dielectric losses, high insulation resistance. The outer sheath have the following characteristics: Fire retardant, low emission dense smoke and halogen free. Adequate resistance to oils. Resistance to sunnlight.
14 AWG, 12 AWG and 10 AWG.
INDECO S.A XLPE/LSZH 600 V - N° Conductors x Gauge + Gauge ground conductor - Year - Sequential length.
Non returnable wooden reels.
Insulation: According to Method 1 Table E2.
Outer sheath: Black.
ASTM B8: Concentric-Lay-Stranded copper conductors, hard, medium-hard, or soft.
ICEA S-95-658: Power cables rated 2000 volts or less for the distribution of electrical energy.
ICEA T-30-520: Conducting Vertical Cable Tray Flame Tests with Theoretical Heat Input Rate of 70,000 B.T.U./Hour.
IEC 60754-1: Test on gases evolved during combustion of materials from cables - Part 1: Determination of the halogen acid gas content.
IEC 60754-2: Test on gases evolved during combustion of materials from cables - Part 2: Determination of acidity (by pH measurement) and conductivity.
IEC 61034: Measurement of smoke density of cables burning under defined conditions.
NES 713: Detremination of the toxicity index of the productsof combustion from small specimens of materials.
NFC 32-200: Conductors and cables with a Regles polyvinyl chloride envelope or sheath.
ASTM G155: Estándar Practice for Operating Xenon Arc light Apparatus for Exposure of Non- metallic materials.
|Conductor material||Soft copper|
|Outer sheath||Halogen free thermoplastic compound - UV Resist.|
|Halogen free||IEC 60754-1|
|Time of application Dielectric strength core to screen DC||5min.|
|U.V resistance||ASTM G155|
|Gases toxicity||NES 713|
|Gases corrosivity||Low pH Corrosivity IEC 60754-2|
|Smoke density||IEC 61034|
|Fire retardant||ICEA T-30-520|
|Maximum operating temperature||90°C|
|Overload maximum core temperature||130°C|
|Short-circuit max. conductor temperature||250°C|
|See all products|