XLPE/LSZH 0,6/1 KV; Multicore; QUELLAVECO
Special application in places with poor ventilation and places public attendance high.
StandardsInternational : IEC 60228; IEC 60332-3-24 Cat.C; IEC 60502-1; IEC 60754-1; IEC 60754-2; IEC 61034; NES 713
National : NTP-IEC 60228; NTP-IEC 60502-1
In low voltage power distribution networks. Special application in places with poor ventilation, direct application in places with high public attendance. It can be installed in ducts or directly buried, in dry and wet places. Not recommended for outdoor installations.
1. Conductor: Soft copper compressed, class 5.
2. Insulation: Cross linked polyethylene XLPE.
3. Outer sheath: HFFR-UV Halogen free thermoplastic compound.
The cable has excellent electric properties. The cross-linked polyethylene insulation allows a higher power capacity current under any operation conditions, lower dielectric losses, high insulation resistance. The Outer sheath have the following characteristics: Fire retardant, low emission dense smoke and halogen free. Adequate resistance to oils. Resistance to sunnlight.
INDECO S.A XLPE/LSZH 0,6/1 KV - N° Conductors x Section - Year - Sequential length.
Non returnable wooden reels.
Insulation: Brown, black and red.
Outer sheath: Black.
NTP-IEC 60228: Conductors of insulated cables.
NTP-IEC 60502-1: Power cables with extruded insulation and their accessories for rated voltages from 1 kV and 3 kV.
IEC 60228: Conductors of insulated cables.
IEC 60502-1: Power cables with extruded insulation and their accessories for rated voltages from 1 kV and 3 kV.
IEC 60332-3-24: Test for vertical flame spread of vertically-mounted bunched wires or cables - Category C.
IEC 60754-1: Test on gases evolved during combustion of materials from cables - Part 1: Determination of the halogen acid gas content.
IEC 60754-2: Test on gases evolved during combustion of materials from cables - Part 2: Determination of acidity (by pH measurement) and conductivity.
IEC 61034: Measurement of smoke density of cables burning under defined conditions.
NES 713: Detremination of the toxicity index of the productsof combustion from small specimens of materials.
NFC 32-200: Conductors and cables with a Regles polyvinyl chloride envelope or sheath.
ASTM G155: Estándar Practice for Operating Xenon Arc light Apparatus for Exposure of Non- metallic materials.
|Conductor material||Soft copper|
|Conductor flexibility||Flexible class 5|
|Outer sheath||Halogen free thermoplastic compound - UV Resist.|
|Halogen free||IEC 60754-1|
|Time of application Dielectric strength core to screen DC||5min.|
|U.V resistance||ASTM G155|
|Gases toxicity||NES 713|
|Gases corrosivity||Low pH Corrosivity IEC 60754-2|
|Smoke density||IEC 61034|
|Fire retardant||IEC 60332-3-24 Cat.C|
|Maximum operating temperature||90°C|
|Overload maximum core temperature||130°C|
|Short-circuit max. conductor temperature||250°C|
|See all products|