StandardsInternational : IEC 60228; IEC 60332-1-2; IEC 60332-3-22 Cat.A; IEC 60754-1; IEC 60840; UIC 895
National : NTP-IEC 60228; SAE J-1127; UL 2556; UL 44
Power distribution in high voltage. As transformer feeders in substations. In power plants, industrial and operation installations, in residential areas and mining installations, in dry or wet locations; where mechanical strength is required.
1. Conductor: Compact stranded soft copper, class 2.
2. Inner semi-conductor: Extruded.
3. Insulation: Cross linked polyethylene XLPE.
4. External semi-conductor: Extruded strippable.
These last three components extruded CV (continuous vulcanization) triple extrusion.
5. Screen: Copper tape (0.127 mm), overlap 50%(longitudinally watertight under and over the screen).
6. Separation sheath: Anti-flame compound polyvinyl chloride PVC + Fire protection tape.
7. Armour: 1350 aluminium wires.
8. Tape: Polyester tape.
9. Outer sheath: Anti-flame compound polyvinyl chloride PVC.
Excellent properties against heat aging. Its armour provides additional mechanical protection. With longitudinally watertight under and over the screen: Resistance to moisture, abrasion and sunlight. Resistance to liquid fuels and oils according to UIC 895 OR. Resistance to sulfuric acid according to SAE J1127. Low halogen content according to IEC 60754-1. Resistant to gasoline GR I according to UL 44. Fire retardant according to IEC 60332-3-22 Cat. A.
185 mm2 and 400 mm2.
INDECO S.A. N2XSYRAY(F) 36/66 kV - Section - Year -Sequential lenght.
Non returnable wooden reels.
Outer sheath: Red.
NTP-IEC 60228: Conductors of insulated cables.
IEC 60228: Conductors of insulated cables.
IEC 60840: Power cables with extruded insulation and their accessories for rated voltages above 30 kV (Um = 36 kV) up to 150 kV (Um = 170 kV) - Test methods and requirements.
IEC 60332-1-2: Test for vertical flame propagation for a single insulated wire or cable - Procedure for 1 kW pre-mixed flame.
UL 2556: Wire and Cable Test Methods. Section 9.3: FT1 (Vertical-Specimen) Flame Test.
IEC 60332-3-22: Test for vertical flame spread of vertically-mounted bunched wires or cables - Category A.
IEC 60754-1: Test on gases evolved during combustion of materials from cables - Part 1: Determination of the halogen acid gas content.
SAE J1127: Standard for Vehicle Cables. Battery cable Clause 6.7 (Compatibility of fluids) - Resistance to Sulfuric Acid.
UL 44: Thermoset-Insulated Wires and Cables. Section 5.17: Gasoline and oil resistance.
UIC 895 OR: Technical specifications for the supply of insulated electric cables for railway vehicles - Oil resistance.
UL 2556:Wire and Cable Test Methods. Section 126.96.36.199:Carbon-Arc and Xenon-Arc Tests- Sunlight resistance.
|Conductor material||Soft copper|
|Material of the inner semi-conductor||Extruded|
|Material of the external semi-conductor||Extruded strippable|
|Armour type||Aluminium Wire|
|Outer sheath||Flame retardant PVC|
|Rated Voltage Uo/U (Um)||36/66 kV|
|Dielectric strength core to screen DC, min.||90.0kV|
|Time of application Dielectric strength core to screen DC||30min.|
|Voltage for partial discharge test||54.0kV|
|Maximal partial discharge test||10pC|
|Mechanical resistance to impacts||Good|
|U.V resistance||UL 2556 - Sunlight Resistance|
|Slightly halogenous||IEC 60754-1|
|Flame retardant||IEC 60332-1-2; FT1|
|Fire retardant||IEC 60332-3-22 Cat.A|
|Fuel resistance||GR I - UL44|
|Oil resistance||UIC 895 OR|
|Longitudinal water tightness||Yes|
|Maximum operating temperature||90°C|
|Overload maximum core temperature||130°C|
|Short-circuit max. conductor temperature||250°C|
|See all products|
Products and services
Docs and info
Wire diameter (mm)