StandardsInternational : IEC 60228; IEC 60811-401; IEC 60811-402; IEC 60811-501; IEC 60811-502; IEC 60811-507; IEC 60811-511
National : GSCC009; NTP-IEC 60228
For installations of urban and rural connections, with voltages up to 1000 V.
1. Conductor: Compact aluminum 1350, class 2.
2. Insulation: Cross linked polyethylene XLPE.
Decreases energy theft, cross-linked polyethylene allows more current capacity and high insulation resistance, lower inductive reactance than with bare conductors, used in overhead distribution lines. Increased safety due to its mechanical strength and toughness of the insulation. Insulators are not necessary for installation. Resistance to abrasion, weather and sunlight.
ENEL DISTRIBUCION PERU - INDECO S.A.- AL-XLPE-0,6/1(1,2) kV - (Nb. Cores x Section) - Year - Month - Sequential length.
Non returnable wooden reels.
Black, see core identification.
NTP-IEC 60228: Conductors of insulated cables.
IEC 60228: Conductors of insulated cables.
GSC009-1: Overhead low voltage distribution cables with rated voltage Uo/U(Umax)= 0,6/1 (1,2) kV.
IEC 60811-201: Measurement of insulation thickness.
IEC 60811-401: Thermal ageing methods -Ageing in an air oven.
IEC 60811-402: Water absorption test.
IEC 60811-501: Test for determining the mechanical properties of insulating and sheating.
IEC 60811-502: Shrinkage test for isolations.
IEC 60811-507: Hot elongation test for crosslinked materials.
IEC 60811-511: Measurement of hot melt index of polyethylene compounds.
|Phase Conductor Type||Aluminium 1350|
|Core identification||Rib markings|
|Rated Voltage Uo/U (Um)||0.6/1 kV|
|Time of application Dielectric strength core to screen DC||15min.|
|Cable flexibility||Class 2 IEC 60228|
|Bending factor when installed||4(xD)|
|Maximum operating temperature||90°C|
|Overload maximum core temperature||130°C|
|Short-circuit max. conductor temperature||250°C|
|See all products|