N2XSYRAY 6/10 kV; IEC 60332-3-22 Cat. A; UIC 895 OR
Power distribution in medium voltage.
StandardsInternational : IEC 60228; IEC 60332-1-2; IEC 60332-3-22 Cat.A; IEC 60502-2; IEC 60754-1; UIC 895
National : NTP-IEC 60228; NTP-IEC 60502-2; SAE J-1127; UL 2556; UL 44
Power distribution in medium voltage. As transformer feeders in substations. In power plants, industrial and operation installations, in residential areas and mining installations, in dry or wet locations; where mechanical strength is required.
1. Conductor: Compact stranded soft copper, class 2.
2. Inner semi-conductor: Extruded.
3. Insulation: Cross linked polyethylene XLPE.
4. External semi-conductor: Extruded strippable.
These last three components extruded CV (continuous vulcanization) triple extrusion in dry cure process.
5. Screen: Copper tapes.
6. Separation sheath: Compound polyvinyl chloride PVC.
7. Armour: 1350 aluminium wires.
8. Fire protection tape.
9. Outer sheath: Anti-flame PVC.
Its armour provides additional mechanical protection. Resistance to abrasion, moisture and sunlight. Resistance to combustible liquids and oils according to UIC 895 OR. Resistance to sulfuric acid according to SAE J1127. Resistance to aliphatic and aromatic hydrocarbon according to UL 44. Fire retardant according to IEC 60332-3-22 Cat. A. Low halogen content according to IEC 60754-1.
INDECO S.A. N2XSYRAY 6/10 kV - Section - Year - Sequential length.
Non returnable wooden reels.
Outer sheath: Red-UV.
NTP-IEC 60228: Conductors of insulated cables.
NTP-IEC 60502-2: Power cables with extruded insulation and their accessories for rated voltages from 6 kV up to 30 kV.
IEC 60228: Conductors of insulated cables.
IEC 60502-2: Power cables with extruded insulation and their accessories for rated voltages from 6 kV up to 30 kV.
IEC 60332-1-2: Test for vertical flame propagation for a single insulated wire or cable - Procedure for 1 kW pre-mixed flame.
UL 2556: Wire and Cable Test Methods. Section 9.3: FT1 (Vertical-Specimen) Flame Test.
IEC 60332-3-22: Test for vertical flame spread of vertically-mounted bunched wires or cables - Category A.
IEC 60754-1: Test on gases evolved during combustion of materials from cables - Part 1: Determination of the halogen acid gas content.
SAE J1127: Standard for Vehicle Cables. Battery cable Clause 6.7 (Compatibility of fluids) - Resistance to Sulfuric Acid.
UL 44: Thermoset-Insulated Wires and Cables. Section 5.17: Gasoline and oil resistance.
UIC 895 OR: Technical specifications for the supply of insulated electric cables for railway vehicles - Oil resistance.
UL 2556:Wire and Cable Test Methods. Section 188.8.131.52:Carbon-Arc and Xenon-Arc Tests- Sunlight resistance.
|Conductor material||Soft copper|
|Material of the inner semi-conductor||Extruded|
|Material of the external semi-conductor||Extruded strippable|
|Screen||Copper tape, helically|
|Armour type||Aluminium Wire|
|Outer sheath||Flame retardant PVC|
|Rated Voltage Uo/U (Um)||6/10 kV|
|Dielectric strength core to screen DC, min.||21.0kV|
|Time of application Dielectric strength core to screen DC||5min.|
|Voltage for partial discharge test||10.4kV|
|Maximal partial discharge test||10pC|
|Mechanical resistance to impacts||Good|
|Flame retardant||IEC 60332-1|
|Fire retardant||IEC 60332-3 Cat.A|
|Slightly halogenous||IEC 60754-1|
|Oil resistance||UIC 895 OR|
|U.V resistance||UL 2556 - Sunlight Resistance|
|Maximum operating temperature||90°C|
|Overload maximum core temperature||130°C|
|Short-circuit max. conductor temperature||250°C|
|See all products|
Products and services
Docs and info
Wire diameter (mm)