N2XRY 0,6/1 kV Multicore with bare ground. conductor
General application as power cable in low voltage.
StandardsInternational : IEC 60228; IEC 60332-1-2; IEC 60502-1; IEC 60811-401; IEC 60811-402; IEC 60811-409; IEC 60811-501; IEC 60811-502; IEC 60811-504; IEC 60811-505; IEC 60811-506; IEC 60811-507; IEC 60811-508; IEC 60811-509
National : NTP-IEC 60228; NTP-IEC 60502-1; UL 2556
General application as power cable. In low voltage distribution power networks, industrial installations, in buildings and operating stations, indoor and outdoor areas. It can be installed in ducts, directly buried in ground, in dry or wet locations where mechanical strength is required.
1. Conductor: Soft copper, class 2.
2. Insulation: Cross linked polyethylene XLPE.
3. Bare grounding conductor: Soft copper, class 2.
4. Inner covering: Compound polyvinyl chloride PVC.
5. Armour: Galvanized steel wires.
6. Tape: Polyester tape.
7. Outer sheath: Compound polyvinyl chloride PVC.
Good electrical and mechanical properties. The cross-linked polyethylene insulation allows greater power capacity under any operation condition, minimum dielectric losses, high insulation resistance. Its armor provides additional mechanical protection. The PVC outer sheath allows an adequate resistance to greases and oils. Resistance to abrasion, moisture and sunlight. Flame retardant.
50 mm2 and 185 mm2.
INDECO S.A. N2XRY 0,6/1 kV - Nb. conductors x Cross section + Gnd. Cross section - Year - Sequential length.
Non returnable wooden reels.
Insulation: Black, white and red.
Outer sheath: Black.
NTP-IEC 60228: Conductors of insulated cables
NPT-IEC 60502-1: Power cables with extruded insulation and their accessories for rated voltages from 1 kV and 3kV.
IEC 60228: Conductors of insulated cables.
IEC 60502-1: Power cables with extruded insulation and their accessories for rated voltages from 1 kV and 3 kV.
IEC 60332-1-2: Test for vertical flame propagation for a single insulated wire or cable - Procedure for 1 kW pre-mixed flame.
IEC 60811-401: Thermal ageing methods -Ageing in an air oven.
IEC 60811-402: Water absorption test.
IEC 60811-409: Mass loss test for thermoplastic insulations and covers.
IEC 60811-501: Test for determining the mechanical properties of insulating and sheating.
IEC 60811-502: Shrinkage test for isolations.
IEC 60811-504: Bending test at low temperature for insulation and covers.
IEC 60811-505: Low temperature elongation test for insulations and covers.
IEC 60811-506: Impact test at low temperature for insulations and covers.
IEC 60811-507: Hot elongation test for crosslinked materials.
IEC 60811-508: High temperature pressure tests for insulations and covers.
IEC 60811-509: Tests of resistance to cracking of the insulations and covers (thermal shock).
UL 2556: Wire and Cable Test Methods. Section 18.104.22.168:Carbon-Arc and Xenon-Arc Tests- Sunlight resistance. Section 9.3: FT1 (Vertical-Specimen) Flame Test.
|Conductor material||Soft copper|
|Armour type||Galvanized steel wires|
|Rated Voltage Uo/U (Um)||0.6/1 kV|
|Time of application Dielectric strength core to screen DC||5min.|
|Mechanical resistance to impacts||Good|
|U.V resistance||UL 2556 - Sunlight Resistance|
|Flame retardant||IEC 60332-1-2; FT1|
|Maximum operating temperature||90°C|
|Overload maximum core temperature||130°C|
|Short-circuit max. conductor temperature||250°C|
|See all products|
Products and services
Docs and info
Wire diameter (mm)