N2XY 0,6/1 kV Single core; IEC 60332-3-22 Cat. A
General application as power cable in low voltage.
StandardsInternational : IEC 60228; IEC 60332-1-2; IEC 60332-3-22 Cat.A; IEC 60502-1; IEC 60754-1; UIC 895
National : NTP-IEC 60228; NTP-IEC 60502-1; SAE J-1127; UL 2556; UL 44
General application as power cable. In low voltage distribution power networks, industrial installations, in buildings and operating stations, indoor and outdoor areas.
1. Conductor: Compact soft copper, class 2.
2. Insulation: Anti-Flame cross linked polyethylene XLPE.
3. Outer sheath: Anti-flame compound polyvinyl chloride PVC.
Resistance to moisture, abrasion and sunlight. Resistance to combustible liquids and oils according to UIC 895 OR and Gasoline Resistant GR I according to UL 44. Resistance to sulfuric acid according to SAE J1127. Low halogen content according to IEC 60754-1. Fire retardant according to IEC 60332-3-22 Cat. A.
From 150 mm2 up to 400 mm2.
INDECO S.A. N2XY 0,6/1 kV - Section - Year - Sequential Length.
Non returnable wooden reels.
Outer sheath: Black.
NTP-IEC 60228: Conductors of insulated cables
NPT-IEC 60502-1: Power cables with extruded insulation and their accesories for rated voltages from 1 kV and 3kV.
IEC 60228: Conductors of insulated cables.
IEC 60502-1: Power cables with extruded insulation and their accesories for rated voltages of 1 kV and 3 kV.
IEC 60332-1-2: Test for vertical flame propagation for a single insulated wire or cable - Procedure for 1 kW pre-mixed flame.
UL 2556: Wire and Cable Test Methods. Section 9.3: FT1 (Vertical-Specimen) Flame Test.
IEC 60332-3-22: Test for vertical flame spread of vertically-mounted bunched wires or cables - Category A.
IEC 60754-1: Test on gases evolved during combustion of materials from cables - Part 1: Determination of the halogen acid gas content.
SAE J1127: Standard for Vehicle Cables. Battery cable Clause 6.7 (Compatibility of fluids) - Resistance to Sulfuric Acid.
UIC 895 OR: Technical specifications for the supply of insulated electric cables for railway vehicles - Oil resistance.
UL 44: Thermoset-Insulated Wires and Cables. Section 5.17: Gasoline and oil resistance.
UL 2556:Wire and Cable Test Methods. Section 220.127.116.11: Carbon-Arc and Xenon-Arc Tests- Sunlight resistance.
|Conductor material||Soft copper|
|Insulating material||Flame retardant XLPE|
|Outer sheath||Flame retardant PVC|
|Rated Voltage Uo/U (Um)||0.6/1 kV|
|Time of application Dielectric strength core to screen DC||5min.|
|Slightly halogenous||IEC 60754-1|
|U.V resistance||UL 2556 - Sunlight Resistance|
|Flame retardant||IEC 60332-1-2; FT1|
|Fire retardant||IEC 60332-3-22 Cat.A|
|Oil resistance||UIC 895 OR|
|Fuel resistance||GR I - UL44|
|Maximum operating temperature||90°C|
|Overload maximum core temperature||130°C|
|Short-circuit max. conductor temperature||250°C|
|See all products|