FREETOX NA2XSAOH 18/30 kV PH; UV Resist.; Outer Sheath and Insulation Nominal Thickness IEC 60502-2; kcmil
Power distribution in medium voltage.
StandardsInternational : IEC 60332-1-2; IEC 60332-3-24 Cat.C; IEC 60502-2; IEC 60684-2; IEC 60754-1; IEC 60754-2; IEC 61034-2
National : ASTM B 231; ICEA S-93-639; NTP-IEC 60502-2; UL 2556
Power distribution in medium voltage. As transformer feeders in substations. In power plants, industrial and operation installations, in residential areas and mining installations, in dry or wet locations.
1. Conductor: Compact stranded 1350 aluminium, class B.
2. Inner semi-conductor: Extruded.
3. Insulation: Cross linked polyethylene XLPE-TR (Tree retardant).
4. External semi-conductor: Extruded strippable.
These last three components extruded CV (continuous vulcanization) triple extrusion in dry cure process.
5. Screen: aluminium 8000 series wires.
6. Tape: Polyester.
7. Outer sheath: HFFR-UV halogen free thermoplastic compound.
Excellent properties against heat aging. The outer sheath has the following characteristics: Fire retardant, low emission dense smoke and halogen free. Adequate resistance to oils. Sunlight resistance.
INDECO S.A. FREETOX NA2XSAOH 18/30 kV - Gauge - PH(Section) - Year - Sequential length.
Non returnable wooden reels.
Outer sheath: Black-UV.
NTP-IEC 60502-2: Power cables with extruded insulation and their accessories for rated voltages from 6 kV up to 30 kV.
ASTM B231: Standard Specification for Concentric-Lay-Stranded Aluminum 1350 Conductors.
IEC 60502-2: Power cables with extruded insulation and their accessories for rated voltages from 6 kV up to 30 kV.
IEC 60332-1-2: Test for vertical flame propagation for a single insulated wire or cable - Procedure for 1 kW pre-mixed flame.
UL 2556: Wire and Cable Test Methods. Section 9.3: FT1 (Vertical-Specimen) Flame Test.
IEC 60332-3-24: Test for vertical flame spread of vertically-mounted bunched wires or cables - Category C.
IEC 60684-2: Flexible insulating sleeving - Part 2: Methods of test.
IEC 60754-1: Test on gases evolved during combustion of materials from cables. Part 1: Determination of the halogen acid gas content.
IEC 60754-2: Test on gases evolved during combustion of materials from cables. Part 2: Determination of acidity (by pH measurement) and conductivity.
IEC 61034-2: Measurement of smoke density of cables burning under defined conditions.
ICEA S-93-639: 5-46 kV Shielded Power Cable for Use in the Transmission and Distribution of Electric Energy. Section 9.4.2: Oil Immersion Test.
UL 2556: Wire and Cable Test Methods. Section 220.127.116.11:Carbon-Arc and Xenon-Arc Tests- Sunlight resistance.
|Conductor material||aluminum Alloy 1350|
|Material of the inner semi-conductor||Extruded|
|Material of the external semi-conductor||Extruded strippable|
|Screen||Aluminum wires 8000 series|
|Outer sheath||Halogen free thermoplastic compound - UV Resist.|
|Halogen free||IEC 60754-1|
|Sheath colour||Black - UV|
|Dielectric strength core to screen DC, min.||63.0kV|
|Time of application Dielectric strength core to screen DC||5min.|
|Voltage for partial discharge test||31.1kV|
|Maximal partial discharge test||10pC|
|U.V resistance||UL 2556 - Sunlight Resistance|
|Oil resistance||ICEA S-93-639|
|Gases toxicity||Low toxicity to IEC 60684-2|
|Gases corrosivity||Low pH Corrosivity IEC 60754-2|
|Smoke density||IEC 61034-2|
|Flame retardant||IEC 60332-1-2; FT1|
|Fire retardant||IEC 60332-3-24 Cat.C|
|Maximum operating temperature||90°C|
|Overload maximum core temperature||130°C|
|Short-circuit max. conductor temperature||250°C|
|See all products|