NA2XSY(F) 35 kV 133% I.L. PH; NRF-024-CFE; NMX-J-142-ANCE
Power distribution in medium voltage.
StandardsInternational : IEC 60332-1-2
National : ICEA S-93-639; UL 2556
Power distribution in medium voltage. As transformer feeders in substations. In power plants, industrial and operation installations, in residential areas and mining installations, in dry or wet locations.
1. Conductor: Compact stranded aluminium 1350, class B.
2. Inner semi-conductor: Extruded.
3. Insulation: Cross linked polyethylene XLPE-TR (Tree retardant).
4. External semi-conductor: Extruded strippable.
These last three components extruded CV (continuous vulcanization) triple extrusion in dry cure process.
5. Screen: Copper wires (longitudinally watertight under and over screen).
6. Outer sheath: Compound polyvinyl chloride PVC.
Excellent properties against heat aging. Insulation level of 133%. Resistance to abrasion, moisture and sunlight. Adequate resistance to greases and oils. Fire retardant.
300 kcmil, 500 kcmil and 1000 kcmil.
INDECO S.A. NA2XSY(F) 35 kV 133% I.L. - Gauge - PH(Screen section) - Year - Sequential length.
Non returnable wooden reels.
Outer sheath: Red.
NMX-J-032-ANCE: Wires and cables – Concentric Lay Stranded Aluminum 1350 cable for electrical purposes – Specifications.
NRF-024-CFE: Single- core power cables rated 5 kV through 35 kV.
NMX-J-142/1-ANCE: Wires and cables - Shielded power cables, rated 5 kV through 35 kV, cross-linked polyethylene or ethylene - propylene rubber insulated - specifications and test methods.
NMX-J-040-ANCE: Determination of the moisture absortion in insulations andprotection jackets of electrical conductors.
NMX-J-091-ANCE: Cold fragility of thermoplastic and thermoset materials.
NMX-J-178-ANCE: Determination of the stress and elongation by tension at the rupture of insulations, semiconductor screens and covers of electrical conductors.
NMX-J-186-ANCE: Accelerated aging in oven to semiconducting screens, insulations and protective covers of electrical conductors.
NMX-J-190-ANCE: Resistance to thermal shock of insulations and thermoplastic protective covers of electrical conductors.
NMX-J-191-ANCE: Deformation by heat of insulations and protective covers of electrical conductors.
NMX-J-193-ANCE: Cold bending of insulations and non-metallic protective covers of electrical conductors.
NMX-J-205-ANCE: Determination of the dissipation factor, ionization factor, in insulated electrical conductors.
IEC 60332-1-2: Test for vertical flame propagation for a single insulated wire or cable - Procedure for 1 kW pre-mixed flame.
UL 2556: Wire and Cable Test Methods. Section 9.3: FT1 (Vertical-Specimen) Flame Test.
ICEA S-93-639: 5-46 kV Shielded Power Cable for Use in the Transmission and Distribution of Electric Energy. Section 9.4.2: Oil Immersion Test.
UL 2556: Wire and Cable Test Methods. Section 188.8.131.52: Carbon-Arc and Xenon-Arc Tests- Sunlight resistance.
|Conductor material||aluminum Alloy 1350|
|Material of the inner semi-conductor||Extruded|
|Material of the external semi-conductor||Extruded strippable|
|Dielectric strength core to screen DC, min.||84.0kV|
|Time of application Dielectric strength core to screen DC||5min.|
|Voltage for partial discharge test||84.0kV|
|Maximal partial discharge test||5pC|
|U.V resistance||UL 2556 - Sunlight Resistance|
|Flame retardant||IEC 60332-1-2; FT1|
|Oil resistance||ICEA S-93-639|
|Maximum operating temperature||90°C|
|Overload maximum core temperature||130°C|
|Short-circuit max. conductor temperature||250°C|
|See all products|