FREETOX N2XSOH 600 V VFD; UV. Resist.
Power or control cable, for use with variable frequency drives (VFD).
StandardsInternational : IEC 60332-1-2; IEC 60332-3-24 Cat.C; IEC 60684-2; IEC 60754-1; IEC 60754-2; IEC 61034-2
National : ASTM B 8; ICEA S-95-658; UL 2556
In factories, substations or power plants where there is an electrical noise or transiet, for control, measuring or signaling systems, for connection between the variable frequency drive (VFD) and the motor; reducing the electromagnetic interferences. Direct application in places with public attendance high.
1. Conductor: Compact soft copper, class B.
2. Insulation: Cross linked polyethylene XLPE.
3. 03 Bare grounding conductor: Soft copper, class B.
4. Inner covering: Halogen free thermoplastic compound.
5. Screen: Copper tape (30 mm x 0,127 mm) overlapped 50%.
6. Outer sheath: HFFR-UV halogen free thermoplastic compound.
The cable has excellent electrical properties. Adequate transient shielding. The cross-linked polyethylene insulation allows a higher power current capacity under any operation conditions, lower dielectric losses and high insulation resistance. The outer sheath have the following characteristics: Fire retardant, low emission of dense smoke and halogen free. Resistance to sunlight. Adequate resistance to oil.
From 8 AWG up to 350 kcmil.
INDECO S.A. FREETOX N2XSOH 600 V - Nb cores x Gauge + Grounding Cond. Gauge - Year - Sequential length.
Non returnable wooden reels.
Insulation: Black, red and blue.
Outer sheath: Black-UV.
ASTM B8: Concentric-lay-stranded copper conductors, hard, medium-hard, or soft.
ICEA S-95-658: Power cables rated 2000 volts or less for the distribution of electrical energy.
IEC 60332-1-2: Test for vertical flame propagation for a single insulated wire or cable - Procedure for 1 kW pre-mixed flame.
UL 2556: Wire and Cable Test Methods. Section 9.3: FT1 (Vertical-Specimen) Flame Test.
IEC 60332-3-24: Test for vertical flame spread of vertically-mounted bunched wires or cables - Category C.
IEC 60684-2: Flexible insulating sleeving - Part 2: Methods of test.
IEC 60754-1: Test on gases evolved during combustion of materials from cables - Part 1: Determination of the halogen acid gas content.
IEC 60754-2: Test on gases evolved during combustion of materials from cables - Part 2: Determination of acidity (by pH measurement) and conductivity.
IEC 61034-2: Measurement of smoke density of cables burning under defined conditions.
ICEA S-95-658: Power cables rated 2000 volts or less for the distribution of electrical energy. Section 6.4.2: Oil Immersion Test.
UL 2556: Wire and Cable Test Methods. Section 126.96.36.199: Carbon-Arc and Xenon-Arc Tests- Sunlight resistance.
|Conductor material||Soft copper|
|Inner sheath||Halogen free flexible thermoplastic compound|
|Screen||Copper tape, helically|
|Outer sheath||Halogen free thermoplastic compound - UV Resist.|
|Sheath colour||Black - UV|
|Halogen free||IEC 60754-1|
|Cable flexibility||Class 2 IEC 60228|
|U.V resistance||UL 2556 - Sunlight Resistance|
|Gases toxicity||Low toxicity to IEC 60684-2|
|Gases corrosivity||Low pH Corrosivity IEC 60754-2|
|Oil resistance||ICEA S-95-658|
|Smoke density||IEC 61034-2|
|Fire retardant||IEC 60332-3-24 Cat.C|
|Flame retardant||IEC 60332-1-2; FT1|
|Electro magnetic interference resistance||Yes|
|Maximum operating temperature||90°C|
|Overload maximum core temperature||130°C|
|Short-circuit max. conductor temperature||250°C|
|See all products|