TTU 2 kV; EEQ Proy: Carolina 2
General use as power cable in low voltage, for fixed installations.
StandardsInternational : IEC 60332-1-2
National : ASTM B 8; ICEA S-95-658; UL 2556
General application as power cable. In low voltage distribution power networks, industrial installations, in buildings and operation stations. In fixed installations, indoor and outdoor areas (trays, gutters, staples). It can be installed in ducts, in dry or wet locations.
1. Conductor: Compact soft copper, class B.
2. Insulation: Low Linear Dendsity Polyethylene LLDPE
3. Outer sheath: Compound Nitrilo-Butadieno Rubber/polyvinyl chloride NBR/PVC.
Good electrical and mechanical properties. The NBR/PVC outer sheath provides greater flexibility and resistance to ozone compared to the traditional PVC jacket. Resistance oils, abrasion and sunlight. Flame retardant.
From 4 AWG up to 350 kcmil.
INDECO S.A. TTU 2 kV - Gauge - Year - Sequential Length.
Non returnable wooden reels.
Outer sheath: Black.
ASTM B8: Concentric-Lay-Stranded copper conductors, hard, medium-hard, or soft.
ICEA S-95-658: Power cables rated 2000 volts or less for the distribution of electrical energy.
IEC 60332-1-2: Test for vertical flame propagation for a single insulated wire or cable - Procedure for 1 kW pre-mixed flame.
UL 2556: Wire and Cable Test Methods. Section 9.3: FT1 (Vertical-Specimen) Flame Test.
ICEA S-95-658: Power cables rated 2000 volts or less for the distribution of electrical energy. Section 6.4.2: Oil: Oil Immersion Test.
UL 2556: Wire and Cable Test Methods. Section 18.104.22.168: Carbon-Arc and Xenon-Arc Tests- Sunlight resistance.
|Conductor material||Soft copper|
|U.V resistance||UL 2556 - Sunlight Resistance|
|Flame retardant||IEC 60332-1-2; FT1|
|Oil resistance||ICEA S-95-658|
|Maximum operating temperature||75°C|
|Overload maximum core temperature||100°C|
|Short-circuit max. conductor temperature||160°C|
|See all products|