N2X2Y 5 kV Class C; UV Resist.; FAA L-824; DGAC-Chile
Power distribution in medium voltage.
StandardsInternational : IEC 60332-1-2; IEC 60684-2; IEC 60754-1; IEC 60754-2; IEC 61034-2
National : ASTM B 8; FAA L-824 Type C; ICEA S-66-524; ICEA S-96-659; UL 2556
Power distribution in medium voltage. As feeders of electrical and electronic systems for use in national airports and airfields, for continuous use, under any weather conditions, whether on the surface of the land exposed to sunlight, buried directly underground or installed in pipelines in wet places.
1. Conductor: Flexible soft copper, class C.
2. Inner semi-conductor: Extruded.
3. Insulation: Cross linked polyethylene XLPE.
4. Outer sheath: Low Linear Dendsity Polyethylene LLDPE-UV.
Excellent properties against heat aging. The outer sheath has the following characteristics: Fire retardant, low emission dense smoke and halogen free. Adequate resistance to oils. Resistance to sunlight.
INDECO S.A. N2X2Y 5 kV Gauge ICEA S-96-659 Month(letters) - Year (numbers)- “Propiedad Fiscal” - Chile DGAC - Sequential length.
Non returnable wooden reels.
Outer sheath: Violet-UV.
ASTM B8: Concentric-Lay-Stranded copper conductors, hard, medium-hard, or soft.
ICEA S-96-659: Nonshielded Cables Rated 2001-5000 V for Use in the Distribution of Electric Energy.
DGAC-Chile: Technical specifications airport cable No. 8 AWG Class 5 kV., National Manufacturing.
FAA L-824 Type C: Specification for L-824 underground electrical cable for airport lighting circuits.
IEC 60332-1-2: Test for vertical flame propagation for a single insulated wire or cable - Procedure for 1 kW pre-mixed flame.
UL 2556: Wire and Cable Test Methods. Section 9.3: FT1 (Vertical-Specimen) Flame Test.
IEC 60684-2: Flexible insulating sleeving - Part 2: Methods of test.
IEC 60754-1: Test on gases evolved during combustion of materials from cables - Part 1: Determination of the halogen acid gas content.
IEC 60754-2: Determination of degree of acidity of gases evolved during the combustion of materials taken from electric cables by measuring pH and conductivity.
IEC 61034-2: Measurement of smoke density of cables burning under defined conditions.
ICEA S-96-659: Nonshielded Cables Rated 2001-5000 V for Use in the Distribution of Electric Energy. Section 7.7.2: Oil Immersion Test.
UL 2556:Wire and Cable Test Methods. Section 184.108.40.206:Carbon-Arc and Xenon-Arc Tests- Sunlight resistance.
ICEA S-66-524: Cross-Linked-Thermosetting-Polyethylene-Insulated Wire and Cable for the Transmission and Distribution of Electrical Energy.
|Conductor material||Soft copper|
|Type of conductor||Class C|
|Material of the inner semi-conductor||Extruded|
|Halogen free||IEC 60754-1|
|Time of application Dielectric strength core to screen DC||5min.|
|U.V resistance||UL 2556 - Sunlight Resistance|
|Oil resistance||ICEA S-96-659|
|Gases toxicity||Low toxicity to IEC 60684-2|
|Gases corrosivity||Low pH Corrosivity IEC 60754-2|
|Smoke density||IEC 61034-2|
|Flame retardant||IEC 60332-1-2; FT1|
|Maximum operating temperature||90°C|
|Overload maximum core temperature||130°C|
|Short-circuit max. conductor temperature||250°C|
|See all products|