StandardsInternational : IEC 60332-1-2
National : ASTM B 231; ICEA S-93-639; ICEA T-34-664; UL 1072; UL 2556
Power distribution in medium voltage. As transformer feeders in substations. In power plants, industrial and operation installations, in residential areas and mining installations, in dry or wet locations.
1. Conductor: Compact stranded aluminium 1350, class B (longitudinally watertight between and over the conductor).
2. Inner semi-conductor: Extruded.
3. Insulation: Cross linked polyethylene XLPE-TR (Tree retardant).
4. External semi-conductor: Extruded strippable.
These last three components extruded CV (continuous vulcanization) triple extrusion in dry cure process.
5. Screen: Copper wires (longitudinally watertight under and over the screen).
6. Outer sheath: Compound polyvinyl chloride PVC.
Excellent properties against heat aging. Insulation level 133%. Longitudinally watertight between and over the conductor; and under and over the screen. Resistance to abrasion, moisture and sunlight. Adequate resistance to greases and oils. Flame retardant.
INDECO S.A. NA2XSY(2OL) 35 kV 133% I.L. - Gauge - PH(Section) - Year - Sequential length.
Non returnable wooden reels.
Outer sheath: Black.
ASTM B231: Standard Specification for Concentric-Lay-Stranded Aluminum 1350 Conductors.
UL 1072: Standard for Medium-Voltage Power Cables.
ICEA S-93-639: 5-46 kV shielded power cable for use in the transmission and distribution of electric energy.
IEC 60332-1-2: Test for vertical flame propagation for a single insulated wire or cable - Procedure for 1 kW pre-mixed flame.
UL 2556: Wire and Cable Test Methods. Section 9.3: FT1 (Vertical-Specimen) Flame Test.
ICEA S-93-639: 5-46 kV Shielded Power Cable for Use in the Transmission and Distribution of Electric Energy. Section 9.4.2: Oil Immersion Test.
UL 2556: Wire and Cable Test Methods. Section 22.214.171.124: Carbon-Arc and Xenon-Arc Tests- Sunlight resistance.
ICEA T-34-664: Test Method for Conducting Longitudinal Water Penetration Resistance Tests on Longitudinal Water Blocked Cables.
|Conductor material||aluminum Alloy 1350|
|Material of the inner semi-conductor||Extruded|
|Material of the external semi-conductor||Extruded strippable|
|Dielectric strength core to screen DC, min.||84.0kV|
|Time of application Dielectric strength core to screen DC||5min.|
|Voltage for partial discharge test||84.0kV|
|Maximal partial discharge test||5pC|
|U.V resistance||UL 2556 - Sunlight Resistance|
|Flame retardant||IEC 60332-1-2; FT1|
|Oil resistance||ICEA S-93-639|
|Longitudinal water tightness||Conductor and screen ICEA T-34-664|
|Maximum operating temperature||90°C|
|Overload maximum core temperature||130°C|
|Short-circuit max. conductor temperature||250°C|
|See all products|