StandardsInternational : IEC 60332-1-2
National : ASTM B 231; ICEA S-95-658; UL 2556
General application as power cable. In low voltage distribution power networks, industrial installations, in buildings and operation stations. In fixed installations, indoor and outdoor areas (trays, gutters, staples). It can be installed in ducts, in dry or wet locations.
1. Conductor: Compact round aluminium 1350, class B.
2. Insulation: Low Linear Dendsity Polyethylene LLDPE
3. Outer sheath: Compound polyvinyl chloride PVC.
Good electrical and mechanical properties. The PVC outer sheath provides an adequate resistance to greases, oils and abrasion. Sunlight resistance and flame retardant.
From 4 AWG up to 4/0 AWG.
INDECO S.A. TTU(AL) 2 kV - Gauge - Year - Sequential Length.
Non returnable wooden reels.
Outer sheath: Black.
ASTM B231: Standard Specification for Concentric-Lay-Stranded Aluminum 1350 Conductors.
ICEA S-95-658: Power cables rated 2000 volts or less for the distribution of electrical energy.
IEC 60332-1-2: Test for vertical flame propagation for a single insulated wire or cable - Procedure for 1 kW pre-mixed flame.
UL 2556: Wire and Cable Test Methods. Section 9.3: FT1 (Vertical-Specimen) Flame Test.
ICEA S-95-658: Power cables rated 2000 volts or less for the distribution of electrical energy. Section 6.4.2: Oil: Oil Immersion Test.
UL 2556: Wire and Cable Test Methods. Section 188.8.131.52: Carbon-Arc and Xenon-Arc Tests- Sunlight resistance.
|Conductor material||aluminum Alloy 1350|
|U.V resistance||UL 2556 - Sunlight Resistance|
|Flame retardant||IEC 60332-1-2; FT1|
|Oil resistance||ICEA S-95-658|
|Maximum operating temperature||75°C|
|Overload maximum core temperature||100°C|
|Short-circuit max. conductor temperature||160°C|
|See all products|