NYY(80°) 600 V Multicore with bare grounding conductor
General use as power cable in low voltage, for fixed installations.
StandardsInternational : IEC 60332-1-2
National : ASTM B 8; ICEA S-95-658; UL 2556
General use as power cable. In low voltage distribution networks, industrial installations, buildings and operating centers. For fixed installations, in indoor areas (trays, gutters, staples), outdoors, in underground ducts or buried direct in ground. It can also be installed in dry or wet locations.
1. Conductor: Compact soft copper, class B.
2. Insulation: Compound polyvinyl chloride PVC.
3. Bare grounding conductor: Soft copper, class B.
4. Filler: Compound polyvinyl chloride PVC.
5. Outer sheath: Compound polyvinyl chloride PVC.
Good electrical and mechanical properties. The PVC outer sheath provides an adequate resistance to grease, oils, abrasion and sunlight. Flame retardant.
From 8 up to 4/0 AWG.
INDECO S.A. NYY(80°) 0,6 kV - (N°Cores x Gauge + ground. gauge)- Year - Sequential Length.
Non returnable wooden reels.
Insulation: White, black and red.
Outer sheath: Black.
ASTM B8: Concentric-Lay-Stranded copper conductors, hard, medium-hard, or soft.
ICEA S-95-658: Power cables rated 2000 volts or less for the distribution of electrical energy.
IEC 60332-1-2: Test for vertical flame propagation for a single insulated wire or cable - Procedure for 1 kW pre-mixed flame.
UL 2556: Wire and Cable Test Methods. Section 9.3: FT1 (Vertical-Specimen) Flame Test.
ICEA S-95-658: Power cables rated 2000 volts or less for the distribution of electrical energy. Section 6.4.2: Oil Immersion Test.
UL 2556: Wire and Cable Test Methods. Section 184.108.40.206: Carbon-Arc and Xenon-Arc Tests- Sunlight resistance.
|Conductor material||Soft copper|
|U.V resistance||UL 2556 - Sunlight Resistance|
|Flame retardant||IEC 60332-1-2; FT1|
|Oil resistance||ICEA S-95-658|
|Maximum operating temperature||80°C|
|Overload maximum core temperature||100°C|
|Short-circuit max. conductor temperature||160°C|
|See all products|