FREETOX NH-80 450/750 V 70 mm2
StandardsInternational : IEC 60228; IEC 60332-1-2; IEC 60332-3-24 Cat.C; IEC 60684-2; IEC 60754-1; IEC 60754-2; IEC 61034-2
National : NTP 370.252; NTP-IEC 60228; UL 2556
Special application in places with poor ventilation, where, in case of fire, the emission of corrosive, toxic gases and smoke threatens life and destroys electrical and electronic equipment, for example in residential buildings, offices, industrial plants, movie, theaters, discotheques, hospitals, airports, underground stations, etc. In case of fire, possible victims have higher chances of surviving because they don't breath in toxic gases and have good visibility to escape the area. They are usually installed in conduits and in indoor areas in tray. Not recommended for outdoor installations. Not recommended for outdoor installations.
Conductor: Compact soft copper, class 2.
Insulation: Halogen free thermoplastic compound HFFR.
Fire retardant, low emission dense smoke and halogen free.
From 16 mm2 up to 300 mm2.
INDECO S.A. FREETOX NH-80 450/750 V - Section - Year - Sequential length..
Non returnable wooden reels.
At the customer's request.
NTP-IEC 60228: Conductors of insulated cables.
NTP 370.252: Thermoplastic and thermoset insulated cables of rated voltages up to and including 450/750 V.
NTP 370.266-3-31: Low voltage electrical cables. Cable with nominal voltage less than or equal to 450/750 V . Part 3-31: Cables with special properties before the fire. Single core cables without cover with halogen-free thermoplastic insulation and low smoke emission.
NTP 370.264-7: Insulation, covering and coating materials for low voltage electrical power cables. Part 7: Halogen-free thermoplastic compounds for insulation.
IEC 60228: Conductors of insulated cables.
IEC 60332-1-2: Test for vertical flame propagation for a single insulated wire or cable - Procedure for 1 kW pre-mixed flame.
UL 2556: Wire and Cable Test Methods. Section 9.3: FT1 (Vertical-Specimen) Flame Test.
IEC 60332-3-24: Test for vertical flame spread of vertically-mounted bunched wires or cables - Category C.
IEC 60684-2: Flexible insulating sleeving - Part 2: Methods of test.
IEC 60754-1: Test on gases evolved during combustion of materials from cables - Part 1: Determination of the halogen acid gas content.
IEC 60754-2: Test on gases evolved during combustion of materials from cables - Part 2: Determination of acidity (by pH measurement) and conductivity.
IEC 61034-2: Measurement of smoke density of cables burning under defined conditions.
|Conductor material||Soft copper|
|Insulation||Halogen free thermoplastic material|
|Halogen free||IEC 60754-1|
|Total number of wires||19|
|Minimum insulation thickness||1.4mm|
|Nominal outer diameter||12.4mm|
|Time of application Dielectric strength core to screen DC||5min.|
|Max. DC resistance of the conductor at 20°C||0.268Ohm/km|
|Perm current rating in duct 30°C||165A|
|Perm current rating in air 30°C||253A|
|Gases toxicity||Low toxicity to IEC 60684-2|
|Gases corrosivity||Low pH Corrosivity IEC 60754-2|
|Smoke density||IEC 61034-2|
|Flame retardant||IEC 60332-1-2; FT1|
|Fire retardant||IEC 60332-3-24 Cat.C|
|Minimum operating temperature||-40°C|
|Maximum operating temperature||80°C|
|Overload maximum core temperature||100°C|
|Short-circuit max. conductor temperature||160°C|