TC(XHHW-2) 600 V 2 AWG
StandardsInternational : FT4 IEEE1202 ; IEC 60332-1-2; IEC 60754-1; UIC 895
National : ASTM B 8; SAE J-1127; UL 1277; UL 2556; UL 44
Power or control cable, for general use, indoor and outdoor applications. For electrical systems in buildings, industrial, mine and commercial. Maximum operating temperature 90°C, in dry or wet locations. Class I, Div . 2 (also Zone 2) hazardous locations per NEC.
1. Conductor: Soft copper, class B.
2. Insulation: Anti-flame cross linked polyethylene XLPE.
3. Outer sheath: Anti-flame compound polyvinyl chloride PVC.
Excellent properties against heat aging. Resistance to moisture, abrasion and sunlight. Resistance to liquid fuels and oils according to UIC 895 OR. Resistance to sulfuric acid according to SAE J1127. Low halogen content according to IEC 60754-1. Resistant to gasoline GR I according to UL 44. Fire retardant according to IEEE 1202/FT-4.
From 14 AWG up to 1000 kcmil.
E325679(UL) TC(XHHW-2) 600V 90°C - Gauge(section mm2) - INDECO S.A. SUN RES-DIR BUR-OIL RES I- 90°C jkt- FT4/IEEE1202 - Year - Sequential length.
Non returnable wooden reels.
Outer sheath: Black, green or costumer request.
ASTM B8: Concentric-Lay-Stranded copper conductors, hard, medium-hard, or soft.
UL 1277: Electrical Power and Control Tray Cables with Optional Optical-Fiber Members.
UL 44: Thermoset-Insulated Wires and Cables.
IEC 60332-1-2: Test for vertical flame propagation for a single insulated wire or cable - Procedure for 1 kW pre-mixed flame.
UL 2556: Wire and Cable Test Methods. Section 9.3: FT1 (Vertical-Specimen) Flame Test.
IEC 60332-3-24: Test for vertical flame spread of vertically-mounted bunched wires or cables - Category C.
IEC 60754-1: Test on gases evolved during combustion of materials from cables - Part 1: Determination of the halogen acid gas content.
IEEE 1202/FT4: Vertical Tray Flame Test.
SAE J1127: Standard for Vehicle Cables. Battery cable Clause 6.7 (Compatibility of fluids) - Resistance to Sulfuric Acid.
UL 44: Thermoset-Insulated Wires and Cables. Section 5.17: Gasoline and oil resistance.
UIC 895 OR: Technical specifications for the supply of insulated electric cables for railway vehicles - Oil resistance.
UL 2556: Wire and Cable Test Methods. Section 126.96.36.199: Carbon-Arc and Xenon-Arc Tests- Sunlight resistance.
|Conductor material||Soft copper|
|Insulating material||Flame retardant XLPE|
|Outer sheath||Flame retardant PVC|
|Conductor cross-section (AWG)||2|
|Minimum insulation thickness||1.14mm|
|Minimum outer sheath thickness||1.14mm|
|Diameter over Sheath||11.5mm|
|Total number of wires||7|
|Max. DC resistance of the conductor at 20°C||0.5335Ohm/km|
|Perm current rating in duct/buried 30°C||130A|
|Perm current rating in air 30°C||190A|
|Time of application Dielectric strength core to screen DC||1min.|
|Cable flexibility||Class B ASTM B8|
|Slightly halogenous||IEC 60754-1|
|U.V resistance||UL 2556 - Sunlight Resistance|
|Flame retardant||IEC 60332-1-2; FT1|
|Fire retardant||FT4/IEEE 1202|
|Oil resistance||UIC 895 OR|
|Fuel resistance||GR I - UL44|
|Maximum operating temperature||90°C|
|Overload maximum core temperature||130°C|
|Short-circuit max. conductor temperature||250°C|