CAPI-MT 25 kV 150 mm2 BLO.HUM.
StandardsInternational : IEC 60228
National : ABNT NBR 11873; NTP-IEC 60228
For overhead primary distribution networks in horizontal arrangements. The installation will be performed in wooded areas in order to reduce the contact of environmental impact. This is not an insulated cable, it is a protected cable.
1. Conductor: Compact stranded aluminium 1350, class 2 (with longitudinally watertight between the conductor).
2. Sheath: Antitracking cross linked polyethylene XLPE compound.
With longitudinally watertight between the conductor. Good properties against heat aging. Resistance to abrasion, moisture, sunlight and to surface discharges (tracking and carbonization). Protection should not be considered as insulation.
From 35 mm2 up to 150 mm2.
INDECO S.A. - CAPI-MT - Section - 25 kV - Aluminum - XLPE - "CABLE NOT ISOLATED, Don't Touch" - Year - Locked - NBR 11873 - Sequential length.
Non returnable wooden reels.
NTP-IEC 60228: Conductors of insulated cables.
IEC 60228: Conductors of insulated cables.
ABNT NBR 11873: Covered cables with polymeric material for overhead distribution lines in spacers for voltages 13,8 kV up to 34,5 kV.
|Conductor material||Aluminum Alloy 1350|
|Minimum outer sheath thickness||4.0mm|
|Diameter over Sheath||22.3mm|
|Total number of wires||19|
|Max. DC resistance of the conductor at 20°C||0.206Ohm/km|
|Perm current rating in air 30°C||493A|
|Time of application Dielectric strength core to screen DC||5min.|
|Maximum operating temperature||90°C|
|Overload maximum core temperature||100°C|
|Short-circuit max. conductor temperature||250°C|