NGY 600 V 500 kcmil
StandardsInternational : IEC 60332-1-2; IEC 60754-1; UIC 895
National : ASTM B 8; ICEA S-95-658; SAE J-1127; UL 2556; UL 44
General application as power cable. In low voltage distribution power networks, industrial installations, in buildings and operation stations. In fixed installations, indoor and outdoor areas (trays, gutters, staples). It can be installed in ducts, in dry or wet locations.
1. Conductor: Soft copper, class B.
2. Insulation: High Ethylene Polyethylene Rubber HEPR.
3. Outer sheath: Anti-flame compound polyvinyl chloride PVC.
HEPR increased safety due to its mechanical strength and toughness of the insulation. Resistance to abrasion, moisture and sunlight. Resistance to liquid fuels and oils according to UIC 895 OR. Resistance to sulfuric acid according to SAE J1127. Low halogen content according to IEC 60754-1. Resistant to gasoline GR I according to UL 44. Fire retardant.
From 12 AWG up to 750 kcmil.
INDECO S.A. NGY 0,6 kV - Gauge - Year - Sequential length.
Non returnable wooden reels.
Outer sheath: To customer request.
ASTM B8: Concentric-Lay-Stranded copper conductors, hard, medium-hard, or soft.
ICEA S-95-658: Power cables rated 2000 volts or less for the distribution of electrical energy.
IEC 60332-1-2: Test for vertical flame propagation for a single insulated wire or cable - Procedure for 1 kW pre-mixed flame.
UL 2556: Wire and Cable Test Methods. Section 9.3: FT1 (Vertical-Specimen) Flame Test.
IEC 60754-1: Test on gases evolved during combustion of materials from cables - Part 1: Determination of the halogen acid gas content.
SAE J1127: Standard for Vehicle Cables. Battery cable Clause 6.7 (Compatibility of fluids) - Resistance to Sulfuric Acid.
UL 44: Thermoset-Insulated Wires and Cables. Section 5.17: Gasoline and oil resistance.
UIC 895 OR: Technical specifications for the supply of insulated electric cables for railway vehicles - Oil resistance.
UL 2556:Wire and Cable Test Methods. Section 188.8.131.52:Carbon-Arc and Xenon-Arc Tests- Sunlight resistance.
|Conductor material||Soft copper|
|Outer sheath||Flame retardant PVC|
|Minimum insulation thickness||1.65mm|
|Minimum outer sheath thickness||1.65mm|
|Diameter over Sheath||25.9mm|
|Total number of wires||37|
|Time of application Dielectric strength core to screen DC||5min.|
|Max. DC resistance of the conductor at 20°C||0.0708Ohm/km|
|Perm current rating in duct/buried 30°C||430A|
|Perm current rating in air 30°C||700A|
|Slightly halogenous||IEC 60754-1|
|U.V resistance||UL 2556 - Sunlight Resistance|
|Flame retardant||IEC 60332-1-2; FT1|
|Oil resistance||UIC 895 OR|
|Fuel resistance||GR I - UL44|
|Maximum operating temperature||90°C|
|Overload maximum core temperature||130°C|
|Short-circuit max. conductor temperature||250°C|