FREETOX TECK90 600 V 4x12+1x14AWG
StandardsInternational : IEC 60332-1-2; IEC 60332-3-24 Cat.C; IEC 60684-2; IEC 60754-1; IEC 60754-2; IEC 61034-2
National : CSA C22.2 N° 03-01; CSA C22.2 N° 131; CSA C22.2 N° 2556; CSA C22.2 N° 38; UL 2556
General application in low voltage distribution networks in operating stations where high mechanical strength is required. The interlocked aluminum armour gives greater flexibility compared to the traditional steel armour and the type of conformation of the same make has a high resistance to loads that could be placed on it.
1. Conductor: Soft copper, class B.
2. Insulation: Cross linked polyethylene XLPE.
3. Bare grounding conductor: Soft copper, class B.
4. Inner covering: HFFR halogen free thermoplastic compound.
5. Armour: Interlocked aluminum tape.
6. Outer sheath: HFFR-UV halogen free thermoplastic compound.
Resistance to abrasion and oils. Resistance to weather and sunlight. Its armour provides additional mechanical protection and provides greater flexibility compared with other types of armour. Fire retardant, low emission of dense smoke and halogen free. Resistance to attack by rodents.
From 12 AWG up to 4/0 AWG.
INDECO S.A. TECK90 (Nb. cores x Gauge phase cond. + Gauge ground. cond.) 0,6 kV - Year - Sequential length.
Non returnable wooden reels.
Insulation: See core identification.
Outer sheath: Black-UV.
CSA C22.2 Nº 131-14: Type TECK 90 cable.
CSA C22.2 Nº 38-14: Thermoset-insulated wires and cables.
CSA C22.2 Nº 03-01: Test methods for electrical wires and cables.
CSA C22.2 Nº 2556-15: Wire and cable test methods.
IEC 60332-1-2: Test for vertical flame propagation for a single insulated wire or cable - Procedure for 1 kW pre-mixed flame.
UL 2556: Wire and Cable Test Methods. Section 9.3: FT1 (Vertical-Specimen) Flame Test.
IEC 60332-3-24: Test for vertical flame spread of vertically-mounted bunched wires or cables - Category C.
IEC 60684-2: Flexible insulating sleeving - Part 2: Methods of test.
IEC 60754-1: Test on gases evolved during combustion of materials from cables - Part 1: Determination of the halogen acid gas content.
IEC 60754-2: Test on gases evolved during combustion of materials from cables - Part 2: Determination of acidity (by pH measurement) and conductivity.
IEC 61034-2: Measurement of smoke density of cables burning under defined conditions.
UL 2556: Wire and Cable Test Methods. Section 184.108.40.206: Carbon-Arc and Xenon-Arc Tests- Sunlight resistance.
|Conductor material||Soft copper|
|Inner sheath||Halogen free compound|
|Armour type||Interlocked aluminum tape|
|Outer sheath||Halogen free thermoplastic compound - UV Resist.|
|Sheath colour||Black - UV|
|Number of conductors||4|
|Halogen free||IEC 60754-1|
|Conductor cross-section (AWG)||12|
|Ground Conductor cross-section (AWG)||14|
|Diameter over inner sheath||11.7mm|
|Minimum insulation thickness||0.76mm|
|Diameter over armour||15.9mm|
|Diameter over Sheath||18mm|
|Minimum outer sheath thickness||1.0mm|
|Inner sheath thickness||1.14mm|
|Total number of wires||7|
|Max. DC resistance of the conductor at 20°C||5.54Ohm/km|
|Perm current rating in air 30°C||16A|
|Dielectric strength core to screen DC, min.||4.0kV|
|Time of application Dielectric strength core to screen DC||1min.|
|Mechanical resistance to impacts||Excellent|
|U.V resistance||UL 2556 - Sunlight Resistance|
|Gases toxicity||Low toxicity to IEC 60684-2|
|Gases corrosivity||Low pH Corrosivity IEC 60754-2|
|Smoke density||IEC 61034-2|
|Fire retardant||IEC 60332-3-24 Cat.C|
|Rodent protection||Corrugated aluminium tape|
|Flame retardant||IEC 60332-1-2; FT1|
|Maximum operating temperature||90°C|
|Overload maximum core temperature||130°C|
|Short-circuit max. conductor temperature||250°C|
|Bending factor when installed||7(xD)|
Docs and info
Number of cores
White + black or black with white numbers for control cable + (yellow or green)
(White or blue) + black + red or black with white numbers for control cable + (yellow or green)
White + black + red + blue or black with white numbers for control cable + (yellow or green)
Black with white numbers for control cable + (yellow or green)