NGY 0,6/1 kV 3x2.5+1x2.5 mm2 FB
StandardsInternational : IEC 60228; IEC 60332-1-2; IEC 60502-1; IEC 60754-1; UIC 895
National : NTP-IEC 60228; NTP-IEC 60502-1; SAE J-1127; UL 2556; UL 44
General application as power cable. In low voltage distribution power networks, industrial installations, in buildings and operation stations. In fixed installations, indoor and outdoor areas (trays, gutters, staples). It can be installed in ducts, in dry or wet locations.
1. Conductor: Flexible soft copper, class 5.
2. Insulation: High Ethylene Polyethylene Rubber HEPR.
3. Insulated grounding conductor: Flexible soft copper, class 5 - HEPR.
4. Filler: PVC compound(as applicable).
5. Outer sheath: Anti-flame compound polyvinyl chloride PVC.
Good electrical and mechanical properties. Resistance to abrasion, moisture and sunlight. Resistance to liquid fuels and oils according to UIC 895 OR. Resistance to sulfuric acid according to SAE J1127. Low halogen content according to IEC 60754-1. Resistant to gasoline GR I according to UL 44. Flame retardant.
From 1,5 mm2 up to 95 mm2.
INDECO S.A. NGY 0.6/1 kV - Nb. Cores x cross section - FB - Year - Sequential length.
Non returnable wooden reels.
Insulation: See core identificacition.
Outer sheath: Black.
NTP-IEC 60228: Conductors of insulated cables.
NPT-IEC 60502-1: Power cables with extruded insulation and their accesories for rated voltages from 1 kV and 3kV.
IEC 60228: Conductors of insulated cables.
IEC 60502-1: Power cables with extruded insulation and their accesories for rated voltages from 1 kV and 3 kV.
IEC 60332-1-2: Test for vertical flame propagation for a single insulated wire or cable - Procedure for 1 kW pre-mixed flame.
UL 2556: Wire and Cable Test Methods. Section 9.3: FT1 (Vertical-Specimen) Flame Test.
IEC 60754-1: Test on gases evolved during combustion of materials from cables - Part 1: Determination of the halogen acid gas content.
SAE J1127: Standard for Vehicle Cables. Battery cable Clause 6.7 (Compatibility of fluids) - Resistance to Sulfuric Acid.
UL 44: Thermoset-Insulated Wires and Cables. Section 5.17: Gasoline and oil resistance.
UIC 895 OR: Technical specifications for the supply of insulated electric cables for railway vehicles - Oil resistance.
UL 2556:Wire and Cable Test Methods. Section 22.214.171.124:Carbon-Arc and Xenon-Arc Tests- Sunlight resistance.
|Conductor material||Soft copper|
|Conductor flexibility||Flexible class 5|
|Outer sheath||Flame retardant PVC|
|Number of cores||3|
|Minimum insulation thickness||0.7mm|
|Ground conductor cross-section||2.5mm²|
|Minimum Insulation thickness of ground cable||0.7mm|
|Minimum outer sheath thickness||1.2mm|
|Diameter over Sheath||10.8mm|
|Rated Voltage Uo/U (Um)||0.6/1 kV|
|Time of application Dielectric strength core to screen DC||5min.|
|Max. DC resistance of the conductor at 20°C||7.98Ohm/km|
|Perm current rating in air 30°C||32A|
|Perm. Current in duct 20°C||33A|
|Permissible current rating buried 20°C||45A|
|Slightly halogenous||IEC 60754-1|
|U.V resistance||UL 2556 - Sunlight Resistance|
|Flame retardant||IEC 60332-1-2; FT1|
|Oil resistance||UIC 895 OR|
|Fuel resistance||GR I - UL44|
|Maximum operating temperature||90°C|
|Overload maximum core temperature||130°C|
|Short-circuit max. conductor temperature||250°C|
Docs and info
Number of cores
Brown + blue; Ground cond: Yellow/Green
Brown + black grey; Ground cond: Yellow/Green
Brown + black grey + blue; Ground cond: Yellow/Green
Black with white numbers for control cable; Ground cond: Yellow/Green