NYSY(80°)-C 0,6/1 kV 7x2,5 mm2
StandardsInternational : IEC 60228; IEC 60332-1-2; IEC 60502-1; IEC 60811-401; IEC 60811-402; IEC 60811-501; IEC 60811-504; IEC 60811-505; IEC 60811-506; IEC 60811-508; IEC 60811-509
National : NTP-IEC 60228; NTP-IEC 60502-1; UL 2556
In factories, substations or power plants; for control, measuring or signaling systems.
1. Conductor: Compressed soft copper, class 2.
2. Insulation: Compound polyvinyl chloride PVC.
3. Inner covering: Compound polyvinyl chloride PVC.
4. Screen: Copper wires.
5. Tape: Polyester.
6. Outer sheath: Compound polyvinyl chloride PVC.
Resistance to moisture, abrasion and sunlight. Adequate resistance to grease and oil. Easy installation. Flame retardant.
1,5 mm2 and 4 mm2.
INDECO S.A. NYSY(80º)-C 0,6/1 kV - Nb. Conductors x Section - PH - Year - Sequential length.
Non returnable wooden reels.
Insulation: Black with white numbers.
Outer sheath: Black.
NTP-IEC 60228: Conductors of insulated cables.
NTP-IEC 60502-1: Power cables with extruded insulation and their accessories for rated voltages from 1 kV and 3 kV.
IEC 60228: Conductors of insulated cables.
IEC 60502-1: Power cables with extruded insulation and their accessories for rated voltages from 1 kV and 3 kV.
IEC 60332-1-2: Test for vertical flame propagation for a single insulated wire or cable - Procedure for 1 kW pre-mixed flame.
UL 2556: Wire and Cable Test Methods. Section 9.3: FT1 (Vertical-Specimen) Flame Test.
IEC 60811-401: Thermal ageing methods. Ageing in an air oven.
IEC 60811-402: Water absorption test.
IEC 60811-501: Tests for determining the mechanical properties of insulating and sheating compounds.
IEC 60811-504: Bending test at low temperature for insulation and sheaths.
IEC 60811-505: Elongation at low temperature for insulations and sheaths.
IEC 60811-506: Impact test at low temperature for insulations and sheaths.
IEC 60811-508: Pressure test at high temperature for insulations and sheaths.
IEC 60811-509: Test for resistance of insulations and sheaths to cracking (heat shock test).
UL 2556:Wire and Cable Test Methods. Section 126.96.36.199: Carbon-Arc and Xenon-Arc Tests- Sunlight resistance.
|Conductor material||Soft copper|
|Core identification||Black cores with white numbers|
|Electrostatic shielding||Helically applied copper wires|
|Number of conductors||7|
|Total number of wires||7|
|Minimum insulation thickness||0.8mm|
|Minimum outer sheath thickness||1.2mm|
|Diameter over Sheath||16.6mm|
|Diameter over inner sheath||12.9mm|
|Diameter over screen||13.9mm|
|Rated Voltage Uo/U (Um)||0.6/1 kV|
|Max. DC resistance of the conductor at 20°C||7.41Ohm/km|
|Dielectric strength core to screen DC, min.||3.5kV|
|Time of application Dielectric strength core to screen DC||5min.|
|Resistance of the screen||2.0Ohm/km|
|Perm current rating in air 30°C||16A|
|Maximum operating temperature||80°C|
|U.V resistance||UL 2556 - Sunlight Resistance|
|Flame retardant||IEC 60332-1-2; FT1|
|Overload maximum core temperature||100°C|
|Short-circuit max. conductor temperature||160°C|