FREETOX N2XOH 0.6/1 kV 3x70+1x35 mm2
StandardsInternational : IEC 60228; IEC 60332-1-2; IEC 60332-3-24 Cat.C; IEC 60502-1; IEC 60684-2; IEC 60754-1; IEC 60754-2; IEC 61034-2
National : ICEA S-95-658; NTP-IEC 60228; NTP-IEC 60502-1; UL 2556
In low voltage power distribution networks. Special application in places with poor ventilation, direct application in places with high public attendance. It can be installed in ducts or directly burried, in dry and wet places.
1. Conductor: Compact soft copper, class 2.
2. Insulation: XLPE cross linked polyethylene.
3. Insulated grounding conductor: Soft copper, class 2 - XLPE.
4. Filler: HFFR halogen free thermoplastic compound (when applicable).
5. Outer sheath: HFFR-UV halogen free thermoplastic compound.
The cable has excellent electric properties. The cross-linked polyethylene insulation allows a higher power capacity current under any operation conditions, lower dielectric losses, high insulation resistance. The outer sheath have the following characteristics: Fire retardant, low emission dense smoke and halogen free. Adequate resistance to oils. Sunlight resistance.
From 6 mm2 up to 300 mm2.
INDECO S.A. FREETOX N2XOH 0,6/1 kV - Nb cores x Section + Grounding Cond. Section - Year - Sequential length.
Non returnable wooden reels.
Insulation: See core identification.
Outer sheath: Black-UV.
NTP-IEC 60228: Conductors of insulated cables.
NTP-IEC 60502-1: Power cables with extruded insulation and their accessories for rated voltages from 1 kV and 3 kV.
IEC 60228: Conductors of insulated cables.
IEC 60502-1: Power cables with extruded insulation and their accessories for rated voltages from 1 kV and 3 kV.
IEC 60332-1-2: Test for vertical flame propagation for a single insulated wire or cable - Procedure for 1 kW pre-mixed flame.
UL 2556: Wire and Cable Test Methods. Section 9.3: FT1 (Vertical-Specimen) Flame Test.
IEC 60332-3-24: Test for vertical flame spread of vertically-mounted bunched wires or cables - Category C.
IEC 60684-2: Flexible insulating sleeving - Part 2: Methods of test.
IEC 60754-1: Test on gases evolved during combustion of materials from cables - Part 1: Determination of the halogen acid gas content.
IEC 60754-2: Test on gases evolved during combustion of materials from cables - Part 2: Determination of acidity (by pH measurement) and conductivity.
IEC 61034-2: Measurement of smoke density of cables burning under defined conditions.
ICEA S-95-658: Power cables rated 2000 volts or less for the distribution of electrical energy. Section 6.4.2: Oil: Oil Immersion Test.
UL 2556:Wire and Cable Test Methods. Section 220.127.116.11:Carbon-Arc and Xenon-Arc Tests- Sunlight resistance.
|Conductor material||Soft copper|
|Outer sheath||Halogen free thermoplastic compound - UV Resist.|
|Sheath colour||Black - UV|
|Halogen free||IEC 60754-1|
|Number of cores||3|
|Ground conductor cross-section||35mm²|
|Minimum insulation thickness||1.1mm|
|Minimum Insulation thickness of ground cable||0.9mm|
|Minimum outer sheath thickness||1.4mm|
|Diameter over Sheath||30.4mm|
|Total number of wires||19|
|Rated Voltage Uo/U (Um)||0.6/1 kV|
|Time of application Dielectric strength core to screen DC||5min.|
|Max. DC resistance of the conductor at 20°C||0.268Ohm/km|
|Perm. Current in duct 20°C||167A|
|Permissible current rating buried 20°C||188A|
|Perm current rating in air 30°C||246A|
|Cable flexibility||Class 2 IEC 60228|
|U.V resistance||UL 2556 - Sunlight Resistance|
|Oil resistance||ICEA S-95-658|
|Gases toxicity||Low toxicity to IEC 60684-2|
|Gases corrosivity||Low pH Corrosivity IEC 60754-2|
|Smoke density||IEC 61034-2|
|Fire retardant||IEC 60332-3-24 Cat.C|
|Flame retardant||IEC 60332-1-2; FT1|
|Maximum operating temperature||90°C|
|Overload maximum core temperature||130°C|
|Short-circuit max. conductor temperature||250°C|
Docs and info
Core Identification L.V with ground cond.
Number of cores
Black + (yellow or green or yellow/green or green/yellow)
White + black, white + red, white + blue, blue + brown, blue + black or black + red + (yellow or green or yellow/green or green/yellow)
White + black + red, black + red + blue, brown + black + grey or blue + brown + black + (yellow or green or yellow/green or green/yellow)
White + black + red + blue, blue + brown + black + grey + (yellow or green or yellow/green or green/yellow)